TeSys VARIO - additional pole - 40 A - for V2Show more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeTeSys device short nameVZ product or component typeAdditional pole performance levelHigh performance poles description1P contacts type and composition1 NO product compatibilityV2 range compatibilityTeSys VARIO switch disconnector network typeACDC network frequency50/60 Hz suitability for isolationYes Complementary mounting locationRightLeft System Voltage690 V AC 50/60 Hz [Uimp] rated impulse withstand voltage8 kV [Ith] conventional free air thermal current40 A [Ithe] conventional enclosed thermal current32 A mechanical durability100000 cycles electrical durability30000 cycles DC-1...5100000 cycles AC-21 connections - terminalsPower circuit: screw clamp terminals cable 0.01 in² (6 mm²) - cable stiffness: flexible - with cable endPower circuit: screw clamp terminals cable 0.02 in² (10 mm²) - cable stiffness: solid tightening torquePower circuit: 18.58 lbf.in (2.1 N.m) - on screw clamp terminals height2.91 in (74 mm) width0.63 in (16 mm) depth1.38 in (35 mm) product weight0.11 lb(US) (0.05 kg) Environment standardsIEC 60947-3 product certificationsGLCSAUL protective treatmentTC IP degree of protectionIP20 conforming to IEC 60529 mechanical robustnessVibrations 10...150 Hz 1 gn IEC 60068-2-6Shocks 11 ms 30 Gn IEC 60068-2-27 ambient air temperature for operation-4...122 °F (-20...50 °C) fire resistance1760 °F (960 °C) conforming to IEC 60695-2-1 Ordering and shipping details Category21730 - V VARIO SWITCH Discount ScheduleCP1 GTIN00785901305668 Nbr. of units in pkg.1 Package weight(Lbs)0.10000000000000001 ReturnabilityN Country of originCZ Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest 178 Catalog 08: Operating Mechanisms and Disconnect Switches (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.