TeSys VARIO - additional neutral block - 40 A - for V02...V2Show more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main rangeTeSys device short nameVZ product or component typeAdditional neutral block performance levelHigh performance poles description1N contacts type and composition1 NO contact operationEarly make, late break product compatibilityV0V01V2V1V02 range compatibilityTeSys VARIO switch disconnector network typeACDC network frequency50/60 Hz Complementary mounting locationRightLeft System Voltage690 V AC 50/60 Hz [Uimp] rated impulse withstand voltage6 kV [Ith] conventional free air thermal current40 A mechanical durability100000 cycles electrical durability30000 cycles DC-1...5100000 cycles AC-21 connections - terminalsScrew clamp terminals cable 0.01 in² (6 mm²) - cable stiffness: flexible - with cable endScrew clamp terminals cable 0.02 in² (10 mm²) - cable stiffness: solid tightening torque18.58 lbf.in (2.1 N.m) - on screw clamp terminals height2.91 in (74 mm) width0.63 in (16 mm) depth1.38 in (35 mm) product weight0.11 lb(US) (0.05 kg) Environment standardsIEC 60947-3 product certificationsULCSAGL protective treatmentTC IP degree of protectionIP20 conforming to IEC 60529 mechanical robustnessShocks 11 ms 15 gn IEC 60068-2-27Vibrations 10...150 Hz 1 gn IEC 60068-2-6 ambient air temperature for operation-4...122 °F (-20...50 °C) fire resistance1760 °F (960 °C) conforming to IEC 60695-2-1 Ordering and shipping details Category21730 - V VARIO SWITCH Discount ScheduleCP1 GTIN00785901164227 Nbr. of units in pkg.1 Package weight(Lbs)0.10000000000000001 ReturnabilityY Country of originCZ Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest 178 Catalog 08: Operating Mechanisms and Disconnect Switches (Version 1.0)Tesys catalogue 2019 - 2020 Motor control and protection components (Version 9.2)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.