Surge Protect - HWA - 80kA - 600Y/347VAC - 3P4W - T4XShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main ProductSurge protection device RangeSurgelogic Device Short NameHWA Complementary Surge Current80 kA per phase System Voltage600Y/347 V AC Phase3 phases Wiring Configuration4-wire ConnectionWire phase and neutral AWG 10 copperWire ground AWG 10 copperWire dry contacts AWG 22 copper MCOV420 V Nominal Discharge Current20 kA Max Number of Poles2 SCCR200 kA Local SignallingStatus LED, green = normal operation per phaseStatus LED, red = fault per phaseAlarm = fault Mounting LocationBottom of enclosure Device MountingSurfaceFlush with fixing kit Height4.8 in (122 mm) Width8.62 in (219 mm) Depth3.11 in (79 mm) Environment Enclosure RatingNEMA 4X Enclosure MaterialPlastic, colour : black StandardsCSA C22.2 No 8 1986UL 1283 ed. 5UL 1449 ed. 4 Ambient Operating149 °F (65 °C) Ordering and shipping details Category08466 - SURGE PROTECTION HWA Discount ScheduleDE1B GTIN00785901406266 Nbr. of units in pkg.1 Package weight(Lbs)10.200000000000001 ReturnabilityN Country of originMX Offer Sustainability RoHS (date code: YYWW)Compliant - since 1743 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP which is known to the State of California to cause cancer and - - - - - - - Substance 2DIDP which is known to the State of California to cause birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest 178 Catalog 06: Surge Protective Devices (Version 1.0)CertificateSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.