Surge Protect - HWA - 100kA - 208Y/120VAC - 3P4W - T4XShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main ProductSurge protection device RangeSurgelogic Device Short NameHWA Complementary Surge Current100 kA per phase System Voltage208Y/120 V AC Phase3 phases Wiring Configuration4-wire ConnectionWire phase and neutral AWG 10 copperWire ground AWG 10 copperWire dry contacts AWG 22 copper MCOV150 V Nominal Discharge Current20 kA Max Number of Poles2 SCCR200 kA Local SignallingStatus LED, green = normal operation per phaseStatus LED, red = fault per phaseAlarm = fault Mounting LocationBottom of enclosure Device MountingSurfaceFlush with fixing kit Height4.8 in (122 mm) Width8.62 in (219 mm) Depth3.11 in (79 mm) Environment Enclosure RatingNEMA 4X Enclosure MaterialPlastic, colour : black StandardsCSA C22.2 No 8 1986UL 1283 ed. 5UL 1449 ed. 4 Ambient Operating149 °F (65 °C) Ordering and shipping details Category08466 - SURGE PROTECTION HWA Discount ScheduleDE1B GTIN00785901946236 Nbr. of units in pkg.1 Package weight(Lbs)5 ReturnabilityY Country of originUS Offer Sustainability RoHS (date code: YYWW) California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP which is known to the State of California to cause cancer and - - - - - - - Substance 2DIDP which is known to the State of California to cause birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest Catalog 06: Surge Protective Devices (Version 1.8)CADSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction SheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.