Modicon M171 Optimized expansion 22 I/OsShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main range of productModicon M171/M172 product or component typeAdditional I/O module product specific applicationHVAC and pumping solution Total inputs/outputs22 discrete input number6 discrete output number1 open collector3 relay outputs SPST with same common2 relay outputs SPST with independent common discrete output current2 A relay analogue input number3 analog input NTC/Pt 10002 configurable analogue output number3 voltage, range: 0...10 V2 PWM/PPM, range: 20 kHz, 12 V, 35 mA Complementary number of port1 LAN expansion bus input/output number5 analog output(s)6 digital input(s)5 analog input(s)6 digital output(s) discrete input logicSink or source (positive/negative) contacts usageVolt-free contacts analogue input typeVoltage 0...1 VVoltage 0...5 V (ratiometric)NTC temperature probe - 50...100 °C - res.: 0.1 °CVoltage 0...10 VCurrent 0...20 mA/4...20 mA sensor power supply12 V DC at 85 mA5 V DC at 20 mA [Us] rated supply voltage24 V12...24 V Ordering and shipping details Category22537 - M171 / M172 HVAC CONTROLLERS Discount SchedulePC12 GTIN003606480752698 Nbr. of units in pkg.1 Package weight(Lbs)0.57999999999999996 ReturnabilityN Country of originIT Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Lead and lead compounds which is known to the State of California to cause cancer and birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD files for TM171EO22R: Modicon M171 Optimized expansion 22 I/Os (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.