View all Type EMA
Surge Protect - EMA - 120kA - 600Y/347VAC - 3P4W - T1 - SWShow more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main ProductSurge protection device RangeSurgelogic Device Short NameEMA Complementary Surge Current120 kA Voltage Rating600Y/347 V AC Number of Phases3 phases Wiring Configuration4-wire ConnectionLugs AWG 10...AWG 3/0 copper 35.40 lbf.in (4 N.m) MCOV420 V Nominal Discharge Current20 kA Max Number of Poles3 Rated Current150 A SCCR200 kA Local SignallingStatus LED green per phase normal operationStatus LED red per phase fault Provided EquipmentAlarm enable/disable switchSwitch-disconnectorSurge counterDry contacts Device MountingSurface Height19.49 in (495 mm) Width9.88 in (251 mm) Depth5.31 in (135 mm) Environment Enclosure RatingNEMA 1 Enclosure Materialgrey painted sheet steel StandardsCSA C22.2 No 8UL 1449:ed. 4UL 1283:ed. 5 Ambient Operating149 °F (65 °C) Ordering and shipping details Category08464 - SURGE PROTECTION EMA Discount ScheduleDE1B Package weight(Lbs)9.30 kg (20.5 lb(US)) ReturnabilityNo Country of originMX Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: Lead and lead compounds which is known to the State of California to cause cancer and birth defects or other reproductive harm. For more information go to www.P65Warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction SheetSizeAdd to My DocumentsHandoutSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.