POWERPACT AUTOMATIC MOULDED CASE SWITCH 600V 1200 A P-FrameShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main product or component typeAutomatic switch range of productPowerPact P trip unit technologyMagnetic circuit breaker typeP-frame Complementary Line Rated Current1200 A System Voltage600 V AC mounting modeUnit mount poles description2P breaking capacity100 kA 240 V AC65 kA 480 V AC25 kA 600 V AC breaking capacity codeJ electrical connectionLugs loadLugs line AWG gaugeAWG 3/0...500 kcmil aluminium/copper 4 terminal identifierAL1200P25K magnetic tripping current10000 A height16.24 in width16.54 in depth14.49 in tightening torque50 N.m 0.15...0.37 in² (95...240 mm²) AWG 3/0...500 kcmil Environment product certificationsIECUL listedCSA Ordering and shipping details Category01215 - PG,H,J,K,L,N UNIT MT BREAKERS Discount ScheduleDE2 Nbr. of units in pkg.1 Package weight(Lbs)32 ReturnabilityY Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1323 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP, which is known to the State of California to cause cancer, and - - - - - - - Substance 2DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest 178 Catalog 07: Miniature and Molded Case Circuit Breakers (Version 1.0)CADSizeAdd to My DocumentsCAD for PJL26000S12: POWERPACT AUTOMATIC MOULDED CASE SWITCH 600V 1200 A P-Frame (Version 1.0)BrochureSizeAdd to My DocumentsHandoutSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.