MOLDED CASE CIRCUIT BREAKER 600V 800AShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact P current sensor rating range800 A Line Rated Current800 A breaking capacity100 kA 240 V AC65 kA 480 V AC25 kA 600 V AC AWG gaugeAWG 3/0...500 kcmil aluminium/copper 3(cable(s)) trip unit technologyElectronic basic ET 1.0I LI Complementary product certificationsIECCSAUL listed System Voltage600 V AC module typeP-Frame mounting locationBusbar mounting modeI-Line poles description3P breaking capacity codeJ electrical connectionI-Line connection lineLugs load continuous current rating80 % height12.86 in depth8.05 in width8.27 in tightening torque50 N.mFor 0.15...0.37 in² (95...240 mm²) (AWG 3/0...500 kcmil)1...1.3 N.m Ordering and shipping details Category01210 - PG,H,J,K,L,N I-LINE BREAKERS Discount ScheduleDE2 GTIN00785901280880 Nbr. of units in pkg.1 Package weight(Lbs)37.140000000000001 ReturnabilityY Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1323 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP, which is known to the State of California to cause cancer, and - - - - - - - Substance 2DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsBrochureSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsHandoutSizeAdd to My DocumentsTripping curvesSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.