MOLDED CASE CIRCUIT BREAKER 600V 1200AShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact P current sensor rating range1200 A Line Rated Current1200 A breaking capacity65 kA 240 V AC35 kA 480 V AC18 kA 600 V AC AWG gaugeAWG 3/0...500 kcmil aluminium/copper 4(cable(s)) trip unit technologyElectronic standard Micrologic 3.0 LI Complementary product certificationsCSAIECUL listed System Voltage600 V AC module typeP-Frame mounting locationBusbar mounting modeI-Line poles description3P breaking capacity codeG electrical connectionI-Line connection lineLugs load continuous current rating80 % device short nameA height16.16 in depth8.05 in width8.27 in Ordering and shipping details Category01210 - PG,H,J,K,L,N I-LINE BREAKERS Discount ScheduleDE2 GTIN00785901550945 Nbr. of units in pkg.1 Package weight(Lbs)32 ReturnabilityY Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP, which is known to the State of California to cause cancer, and - - - - - - - Substance 2DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsBrochureSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsHandoutSizeAdd to My DocumentsTripping curvesSizeAdd to My DocumentsMicrologic 2.0, 3.0, 5.0, and 6.0 Std, A, P, and H Trip Unit - Instantaneous Override Values (Version 1.0)Micrologic 3.0 A Trip Unit Characteristic Trip Curve No. 613-8 (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.