ClimaSys indoor slim cooling unit block - 1100W at 230 V - ULShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeClimaSys product nameCU product or component typeSlim cooling unit block mounting typeDoor of enclosure type of installationIndoor product destinationFor enclosure mounting modeBy screws input voltage230 V 50/60 Hz Phase1 phase cooling power2934 Btu/h 50/60 Hz L35-L503753 Btu/h 50/60 Hz L35-L35 Complementary height66.77 in (1696 mm) width19.49 in (495 mm) depth7.68 in (195 mm) Line Rated Current4.8 A inrush current11 A power consumption in W660 W at 50/60 Hz, L35-L35790 W at 50/60 Hz, L35-L50 energy efficiency ratio1.7 control typeElectronic controller temperature setting range68...122 °F (20...50 °C) ambient air temperature for operation50 °C, maximum20...46 °C, inside the enclosure20...50 °C, outside the enclosure Noise level64 dB conforming to EN/ISO 3746 pressure406.11 psi (28 bar) Flow rateExternal circuit : 860 m3/h at 50/60 HzInternal circuit : 860 m3/h at 50/60 Hz product weight110.23 lb(US) (50 kg) cooling gas typeR134a (0.5 kg) Type of filterOptional external circuit filter protection typeThermal protection: T 6 AShort-circuit protection (magnetic) : materialSteel colourGrey RAL 7035 Environment product certificationsUL IP degree of protectionIP34 on the external circuit conforming to IEC 60529IP55 on the internal circuit conforming to IEC 60529 Ordering and shipping details Category80036 - ENCLOSURE SYSTEMS ACCESSORIES Discount ScheduleES1 GTIN003606480676888 Nbr. of units in pkg.1 Package weight(Lbs)110.2 ReturnabilityN Offer Sustainability RoHS (date code: YYWW)Compliant - since 0940 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh California proposition 65WARNING: Cancer and Reproductive Harm - www.P65Warnings.ca.gov
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsCAD files for NSYCUS1K1UL: Slim cooling units (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.