ClimaSys standard cooling unit roof of enclosure - 2050W at 400 VShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeClimaSys product nameCU product or component typeCooling unit mounting typeRoof of enclosure type of installationIndoor product destinationFor enclosure mounting modeBy screws input voltage460 V 60 Hz Phase3 phases cooling power6990 Btu/h 60 Hz L35-L355320 Btu/h 60 Hz L35-L50 Complementary height16.34 in (415 mm) width567 mm depth401 mm Line Rated Current1.9 A inrush current10 A power consumption in W990 W at 60 Hz, L35-L351190 W at 60 Hz, L35-L50 energy efficiency ratio2.1 control typeElectronic controller temperature setting range20...45 °C ambient air temperature for operation20...45 °C, outside the enclosure45 °C, maximum20...45 °C, inside the enclosure Noise level65 dB pressure362.59 psi (25 bar) Flow rateExternal circuit : 1820 m3/h at 60 HzInternal circuit : 1050 m3/h at 60 Hz product weight114.64 lb(US) (52 kg) cooling gas typeR134a (0.55 kg) Type of filterOptional external circuit filter protection typeThermal protection: T 6 AShort-circuit protection (magnetic) : materialSteel colourGrey RAL 7035 Environment product certificationsUL standardsDIN 3168 IP degree of protectionIP54 on the internal circuit conforming to IEC 60529IP34 on the external circuit conforming to IEC 60529 Ordering and shipping details Category80036 - ENCLOSURE SYSTEMS ACCESSORIES Discount ScheduleES1 GTIN003606480654053 Nbr. of units in pkg.1 Package weight(Lbs)114.61 ReturnabilityN Offer Sustainability RoHS (date code: YYWW) REACh California proposition 65WARNING: Cancer and Reproductive Harm - www.P65Warnings.ca.gov
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsCAD Drawing - 3D STP Format - ClimaSys standard cooling unit roof of enclosure - UL standard - 2050W at 400 V (Version 1.0)CAD files for NSYCU2K3P4RUL: Top-mounting models (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.