ClimaSys standard cooling unit side of enclosure - 1600W at 400...440 VShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeClimaSys product nameCU product or component typeCooling unit mounting typeSide type of installationIndoor product destinationFor enclosure mounting modeBy screws input voltage400...460 V 50/60 Hz Phase2 phases cooling power5460 Btu/h 50/60 Hz L35-L354200 Btu/h 50/60 Hz L35-L50 Complementary height999 mm width15.94 in (405 mm) depth237 mm Line Rated Current2.9 A inrush current11 A power consumption in W840 W at 50/60 Hz, L35-L35960 W at 50/60 Hz, L35-L50 energy efficiency ratio1.9 control typeElectronic controller temperature setting range68...122 °F (20...50 °C) ambient air temperature for operation50 °C, maximum20...46 °C, inside the enclosure20...50 °C, outside the enclosure Noise level65 dB pressure362.59 psi (25 bar) Flow rateInternal circuit : 570 m3/h at 50/60 HzExternal circuit : 1050 m3/h at 50/60 Hz product weight92.59 lb(US) (42 kg) cooling gas typeR134a (0.45 kg) Type of filterOptional external circuit filter protection typeThermal protection: T 6 AShort-circuit protection (magnetic) : materialSteel colourGrey RAL 7035 Environment product certificationsUL standardsDIN 3168 IP degree of protectionIP34 on the external circuit conforming to IEC 60529IP55 on the internal circuit conforming to IEC 60529 Ordering and shipping details Category80036 - ENCLOSURE SYSTEMS ACCESSORIES Discount ScheduleES1 GTIN003606480653742 Nbr. of units in pkg.1 Package weight(Lbs)92.570000000000007 ReturnabilityN Offer Sustainability RoHS (date code: YYWW) REACh California proposition 65WARNING: Cancer and Reproductive Harm - www.P65Warnings.ca.gov
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsCAD Drawing - 3D STP Format - ClimaSys standard cooling unit side of enclosure - UL standard - 1600W at 400...440 V (Version 1.0)CAD files for NSYCU1K62P4UL: Side-mounting models and floor-standing models (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.