ClimaSys standard cooling unit roof of enclosure - 1550W at 230 VShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeClimaSys product nameCU product or component typeCooling unit mounting typeRoof of enclosure type of installationIndoor product destinationFor enclosure mounting modeBy screws input voltage230 V 50/60 Hz Phase1 phase cooling power5290 Btu/h 50/60 Hz L35-L354090 Btu/h 50/60 Hz L35-L50 Complementary height16.34 in (415 mm) width567 mm depth401 mm Line Rated Current4.5 A inrush current18 A power consumption in W810 W at 50/60 Hz, L35-L35930 W at 50/60 Hz, L35-L50 energy efficiency ratio1.9 control typeElectronic controller temperature setting range68...122 °F (20...50 °C) ambient air temperature for operation50 °C, maximum20...46 °C, inside the enclosure20...50 °C, outside the enclosure Noise level65 dB pressure362.59 psi (25 bar) Flow rateInternal circuit : 860 m3/h at 50/60 HzExternal circuit : 1820 m3/h at 50/60 Hz product weight97 lb(US) (44 kg) cooling gas typeR134a (0.54 kg) Type of filterOptional external circuit filter protection typeThermal protection : T 10 AShort-circuit protection (magnetic) : materialSteel colourGrey RAL 7035 Environment product certificationsUL standardsDIN 3168 IP degree of protectionIP54 on the internal circuit conforming to IEC 60529IP34 on the external circuit conforming to IEC 60529 Ordering and shipping details Category80036 - ENCLOSURE SYSTEMS ACCESSORIES Discount ScheduleES1 GTIN003606480654039 Nbr. of units in pkg.1 Package weight(Lbs)96.980000000000004 ReturnabilityN Offer Sustainability RoHS (date code: YYWW) REACh California proposition 65WARNING: Cancer and Reproductive Harm - www.P65Warnings.ca.gov
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsCAD Drawing - 3D STP Format - ClimaSys standard cooling unit top of enclosure - UL standard - 1550W at 230 V (Version 1.0)CAD files for NSYCU1K5RUL: Top-mounting models (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.