NF Pnlbrd Interior 600A, 3 PH, 4 Wire, 30 CCT, Mn Lug, CuShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main load center typeMain lugs Branch Circuit Breaker TypeEDB/EDG/EDJ connections - terminalsLug line AWG 1/0...750 kcmil aluminiumLug neutral AWG 1/0...750 kcmil aluminium Busbar MaterialCopper Complementary number of spaces30 Enclosure Nominal Height50 in Enclosure Nominal Width20 in Enclosure Nominal Width5.75 inFor NEMA 1 enclosure6.5 inFor NEMA 3R/5/12 enclosure Line Rated Current600 A wiring configuration4-wire Phase3 phases System Voltage480Y/277 V AC tightening torque31.07...33.9 N.m 53.48...380 mm² (AWG 1/0...750 kcmil)31.07...33.9 N.m 53.48...177.3 mm² (AWG 1/0...350 kcmil)62.14 N.m 53.48...380 mm² (AWG 1/0...750 kcmil)62.14 N.m 53.48...152 mm² (AWG 1/0...300 kcmil)42.37 N.m 53.48...380 mm² (AWG 1/0...750 kcmil)42.37 N.m 53.48...152 mm² (AWG 1/0...300 kcmil) Environment standardsUL 67CSA C22.2 Ordering and shipping details Category08350 - NF MLO INTERIOR RTA Discount SchedulePE1A GTIN00785901116196 Nbr. of units in pkg.1 Package weight(Lbs)31 ReturnabilityN Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Nickel compounds which is known to the State of California to cause cancer and - - - - - - - Substance 2Bisphenol A (BPA) which is known to the State of California to cause birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsData BulletinSizeAdd to My DocumentsSpecification guideSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction SheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.