PowerPact M Molded CASE CIRCUIT BREAKER 600V 800A 3PShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact M breaking capacity codeG trip unit technologyElectronic basic ET 1.0 LI Complementary current sensor rating range800 A Line Rated Current800 A System Voltage600 V AC mounting modeI-Line poles description3P breaking capacity65 kA 240 V AC35 kA 480 V AC18 kA 600 V AC continuous current rating80 % electrical connectionI-Line connection lineLugs load AWG gaugeAWG 3/0...500 kcmil aluminium/copper 3(cables(s)) magnetic tripping current1600...8000 A Environment product certificationsCSAIECUL listed Ordering and shipping details Category01200 - MG, MJ I-LINE BREAKER Discount ScheduleDE2 GTIN00785901496793 Nbr. of units in pkg.1 Package weight(Lbs)29.140000000000001 ReturnabilityY Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP, which is known to the State of California to cause cancer, and - - - - - - - Substance 2DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD for MGA36800: PowerPact M Molded CASE CIRCUIT BREAKER 600V 800A 3P (Version 1.0)BrochureSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction SheetSizeAdd to My DocumentsLug Kits for PowerPact™ M- and P-Frame and Compact™ NS630b–NS1250 (Version 2)Handle Extension for CK and PowerPact™ P- and M-frame Circuit Breakers (Version 1)HandoutSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.