View all TeSys F Contactors
TeSys F - contactor coil - LX1FK - 220...230 V AC 40...400 HzShow more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main rangeTeSys product or component typeContactor coil device short nameLX1FK range compatibilityTeSys F LC1F contactor product compatibilityLC1F500 control circuit typeAC 40...400 Hz [Uc] control circuit voltage220...230 V AC 40...400 Hz average resistance35.5 Ohm inrush 68 °F (20 °C)915 Ohm holding 68 °F (20 °C) inductance of closed circuit4.55 H operating time100...170 ms opening40...75 ms closing mechanical durability10 Mcycles maximum operating rate2400 cyc/h 131 °F (55 °C) Complementary coil technologyWithout built-in suppressor module control circuit voltage limitsOperational 0.85...1.1 Uc 40...400 Hz 131 °F (55 °C))Drop-out 0.3...0.5 Uc 40...400 Hz 131 °F (55 °C)) inrush power in VA1100 VA 40...400 Hz 0.9 68 °F (20 °C)) hold-in power consumption in VA18 VA 40...400 Hz 0.3 68 °F (20 °C)) heat dissipation18 W 40...400 Hz Environment ambient air temperature for operation23…131 °F (-5…55 °C) net weight2.54 lb(US) (1.15 kg) Ordering and shipping details Category22341 - CONTACTOR,D,K,&F ACCESS Discount ScheduleI12 GTIN00785901226895 Package weight(Lbs)1.19 kg (2.62 lb(US)) ReturnabilityYes Country of originCZ Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveNot applicable, out of EU RoHS legal scope Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsTesys catalogue 2019 - 2020 Motor control and protection components (Version 9.2)Control Panel Technical Guide - How to quickly design optimized contactor assemblies (Version 1.1)
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.