View all TeSys D Contactors
TeSys D - contactor coil - LX1D8 - 480 V AC 50/60 Hz for 115 & 150 A contactorShow more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main rangeTeSys product or component typeContactor coil device short nameLX1D8 control circuit typeAC 50/60 Hz [Uc] control circuit voltage480 V AC 50/60 Hz average resistance32249 Ohm 68 °F (20 °C) inductance of closed circuit938.41 H product compatibilityLC1D115LC1D150 mechanical durability8 Mcycles maximum operating rate1200 cyc/h 140 °F (60 °C) Complementary coil technologyWithout built-in suppressor module control circuit voltage limitsDrop-out 0.3...0.5 Uc 50/60 Hz 131 °F (55 °C))Operational 0.8...1.15 Uc 50/60 Hz 131 °F (55 °C)) inrush power in VA280…350 VA 60 Hz 0.9 68 °F (20 °C))280…350 VA 50 Hz 0.9 68 °F (20 °C)) hold-in power consumption in VA2…18 VA 60 Hz 0.9 68 °F (20 °C))2…18 VA 50 Hz 0.9 68 °F (20 °C)) heat dissipation3…4.5 W 50/60 Hz Environment ambient air temperature for operation23…140 °F (-5…60 °C) Ordering and shipping details Category22341 - CONTACTOR,D,K,&F ACCESS Discount ScheduleI12 GTIN00785901303756 Package weight(Lbs)0.32 kg (0.7 lb(US)) ReturnabilityYes Country of originCZ Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: Antimony oxide & Antimony trioxide, which is known to the State of California to cause cancer. For more information go to www.p65warnings.ca.gov Contractual warranty Warranty18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest 178 Catalog 18: Contactors and Starters-IEC (Version 1.0)Control Panel Technical Guide - How to quickly design optimized contactor assemblies (Version 1.1)Tesys catalogue 2019 - 2020 Motor control and protection components (Version 9.2)
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.