View all PowerPact L-Frame Molded Case Circuit Breakers
PowerPact L I-Line Circuit Breaker,Micrologic5.3E,600A,3P,600V,100kAShow more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Main product or component typeCircuit breaker range of productPowerPact L Trip Unit TypeElectronic, energy, Micrologic 5.3 E, LSI Interrupt CodeR Complementary protection technologyCurrent limiter Line Rated Current600 A Number of Poles3P Interrupt Rating200 kA 240 V AC200 kA 480 V AC100 kA 600 V AC Voltage Rating600 V AC continuous current rating80 % mounting modeI-Line electrical connectionI-Line connection lineLugs load Wire SizeAWG 3/0...500 kcmil aluminium/copper)2 Terminal TypeAL600LF52K3 I-Line Phase ConnectionABC height373.38 mm (14.7 in) width150.88 mm (5.94 in) depth167.89 mm (6.61 in) tightening torque38.94…442.54 lbf.in (4.4…50 N.m) 0.15…0.37 in² (95…240 mm²) AWG 3/0...500 kcmil)38.94…442.54 lbf.in (4.4…50 N.m) AWG 3/0...500 kcmil) Environment product certificationsCCCUL listedCENMXCSA Ordering and shipping details Category01111-L HIGH INTERUPT I-LINE BREAKER/SW Discount ScheduleDE2 Package weight(Lbs)15.00 lb(US) (6.804 kg) ReturnabilityYes Country of originUS Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: DINP, which is known to the State of California to cause cancer, and DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm.For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Contractual warranty Warranty18 months
Documents and DownloadsLanguage
End of Life InformationSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.