TeSys LRD thermal overload relays - 60...100 A - class 20Show more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main rangeTeSys product nameTeSys LRD product or component typeElectronic thermal overload relay device short nameLR9D relay applicationMotor protection product compatibilityLC1D115NSX circuit breakerLC1D150 network typeAC signalling functionAlarm thermal protection adjustment range60...100 A [Ui] rated insulation voltage1000 V power circuit conforming to IEC 60947-4-1600 V power circuit conforming to CSA600 V power circuit conforming to UL Complementary network frequency50...60 Hz [Us] rated supply voltage24 V DC supply voltage limits17...32 V mounting supportRailUnder contactor tripping threshold1.05 +/- 0.06 In alarm conforming to IEC 60947-4-11.12 +/- 0.06 In de-energisation conforming to IEC 60947-4-1 [Ith] conventional free air thermal current5 A for signalling circuit System Voltage690 V 50...60 Hz associated fuse rating5 A gG for signalling circuit [Uimp] rated impulse withstand voltage6 kV conforming to IEC 61000-4-5 phase failure sensitivityTripping in 4 s +/- 20 % conforming to IEC 60947-4-1 control typeRed push-button stopBlue push-button for reset mode temperature compensation-4...140 °F (-20...60 °C) switching capacity in mA0...150 mA voltage drop<= 2.5 V closed state connections - terminalsPower circuit: barsControl circuit : screw clamp terminals 1 cable(s) 0.5...1.5 mm² flexible without cable endControl circuit : screw clamp terminals 2 cable(s) 0.5...1.5 mm² flexible without cable endAlarm circuit : screw clamp terminals 1 cable(s) 0.5...1.5 mm² flexible without cable end tightening torqueAlarm circuit : 0.45 N.m on screw clamp terminalsPower circuit : 18 N.m on bars screw : M8Control circuit : 1.2 N.m on screw clamp terminals depth5.2 in (132 mm) product weight1.95 lb(US) (0.885 kg) Environment protective treatmentTH conforming to IEC 60068 IP degree of protectionIP20 conforming to IEC 60529 ambient air temperature for operation-4...140 °F (-20...60 °C) without derating conforming to IEC 60947-4-1 ambient air temperature for storage-76...158 °F (-60...70 °C) operating altitude<= 6561.68 ft (2000 m) without derating mechanical robustnessVibrations 2 Gn, 5...300 Hz IEC 60068-2-6Shocks 13 Gn for 11 ms IEC 60068-2-7 dielectric strength6 kV at 50 Hz conforming to IEC 60255-5 standardsEN 60947-4-1IEC 255-8IEC 255-17VDE 0660IEC 60947-4-1 product certificationsCSA 22-2UL 508 Ordering and shipping details Category22347 - CONTACTOR,D-LINE,OVERLOADS-NEW Discount ScheduleI12 GTIN00785901435426 Nbr. of units in pkg.1 Package weight(Lbs)2.1899999999999999 ReturnabilityY Country of originFR Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1001 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Antimony oxide & Antimony trioxide, which is known to the State of California to cause cancer. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest 178 Catalog 18: Contactors and Starters-IEC (Version 1.0)Data BulletinSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for LR9D5567: TeSys LRD thermal overload relays - 60...100 A - class 20 (Version 2.0)CAD for LR9D5567: TeSys LRD thermal overload relays - 60...100 A - class 20 (Version 1.0)TeSys D Differential thermal overload relays Class 10, 10A or 20 for connection by bars or connectors (Version 1.0)Thermal motor - D range - Electronic (Version 1.0)CertificateSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.