TeSys K - differential thermal overload relays - 0.8...1.2 A - class 10AShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main rangeTeSys product nameTeSys LRK product or component typeDifferential thermal overload relay device short nameLR2K relay applicationMotor protection product compatibilityLC1KLP1KLC7KLP4K network typeACDC thermal overload classClass 10A conforming to IEC 60947-4-1 thermal protection adjustment range0.8...1.2 A [Ui] rated insulation voltage600 V power circuit conforming to CSA C22.2 No 14690 V power circuit conforming to BS 4941690 V power circuit conforming to IEC 60947750 V power circuit conforming to VDE 0110 group C Complementary network frequency<= 400 Hz mounting supportPlate with specific accessoriesRail with specific accessoriesUnder contactor auxiliary contact composition1 NO + 1 NC [Ith] conventional free air thermal current6 A for signalling circuit System Voltage<= 690 V power circuit690 V AC AC-15 signalling circuit250 V DC DC-13 signalling circuit associated fuse rating6 A gG for signalling circuit conforming to VDE 06606 A gG for signalling circuit conforming to IEC 60947 [Uimp] rated impulse withstand voltage6 kV power dissipation per pole2 W phase failure sensitivityYes conforming to IEC 60947-4-1 local signallingTrip indicator (yellow) control typeRed push-button trip test functionBlue push-button stop and manual resetSelector switch manual or automatic reset mode connections - terminalsScrew clamp terminals 1 cable(s) 0...0.01 in² (1.5...4 mm²) - cable stiffness: solidScrew clamp terminals 1 cable(s) 0...0.01 in² (0.75...4 mm²) - cable stiffness: flexible - without cable endScrew clamp terminals 1 cable(s) 0...0 in² (0.34...2.5 mm²) - cable stiffness: flexible - with cable endScrew clamp terminals 2 cable(s) 0...0.01 in² (1.5...4 mm²) - cable stiffness: solidScrew clamp terminals 2 cable(s) 0...0.01 in² (0.75...4 mm²) - cable stiffness: flexible - without cable endScrew clamp terminals 2 cable(s) 0...0 in² (0.34...1.5 mm²) - cable stiffness: flexible - with cable end tightening torque11.5 lbf.in (1.3 N.m) - on screw clamp terminals - with screwdriver Philips No 211.5 lbf.in (1.3 N.m) - on screw clamp terminals - with screwdriver flat Ø 6 mm height2.28 in (58 mm) width1.77 in (45 mm) depth2.56 in (65 mm) product weight0.32 lb(US) (0.145 kg) Environment standardsBS 4941IEC 60947NF C 63-650VDE 0660 product certificationsCSAUL protective treatmentTC conforming to IEC 60068TC conforming to DIN 50016 IP degree of protectionIP2x conforming to IEC 60529 ambient air temperature for operation-4...131 °F (-20...55 °C) without derating conforming to IEC 60947-22...140 °F (-30...60 °C) with derating conforming to IEC 60947 ambient air temperature for storage-40...158 °F (-40...70 °C) operating altitude6561.68 ft (2000 m) without derating fire resistance1562 °F (850 °C) conforming to IEC 60695-2-1 flame retardanceV1 conforming to UL 94Requirement 2 conforming to NF F 16-101Requirement 2 conforming to NF F 16-102 mechanical robustnessShocks NO contact 10 Gn for 11 ms conforming to IEC 60068-2-27Shocks NC contact 10 Gn for 11 ms conforming to IEC 60068-2-27Vibrations NO contact 2 Gn, 5...300 Hz conforming to IEC 60068-2-6Vibrations NC contact 2 Gn, 5...300 Hz conforming to IEC 60068-2-6 Ordering and shipping details Category22324 - CONTACTOR,K-LINE,OVERLOADS Discount ScheduleI12 GTIN00785901883517 Nbr. of units in pkg.1 Package weight(Lbs)0.34000000000000002 ReturnabilityY Country of originCZ Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Antimony oxide & Antimony trioxide, which is known to the State of California to cause cancer. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsCADSizeAdd to My DocumentsThermal overload relays adjustable from 0,11A to 16A.Thermal overload relays adjustable from 0,11A to 16A.
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.