TeSys LK - disconnect switch -3P - 1000A - ACShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeTeSys product nameTeSys LK product or component typeDisconnect Switch disconnector device typeNon-fusible disconnect switch suitability for isolationYes Complementary poles description3P network typeAC network frequency50/60 Hz [Ie] rated operational current1000 A conforming to CSA1000 A conforming to UL630 A (AC-22A) at 690 V AC conforming to IEC400 A (AC-23A) at 690 V AC conforming to IEC1000 A (AC-22A) at 400 V AC conforming to IEC1000 A (AC-23A) at 400 V AC conforming to IEC System Voltage600 V AC 50/60 Hz [Ui] rated insulation voltage1000 V control typeRotary handle type of operating handleExternal frontalExternal right side mounting supportPlate [Uimp] rated impulse withstand voltage12 kV conforming to IEC rated power in W560 kW at 500 V400 kW at 690 V560 kW at 400 V rated power in hp200 hp at 240 V 480 A AC500 hp at 480 V 590 A AC500 hp at 600 V 472 A AC [Icw] rated short-time withstand current75 kA mechanical durability3500 cycles electrical durability500 cycles connections - terminalsBars 2 x 50 x 5 mmLugs-ring terminals 2 cable(s) 34 mm² height12.6 in (320 mm) width14.57 in (370 mm) depth5.51 in (140 mm) Environment standardsUL98CSA C22.2 No 4IEC 60947-3 product certificationsCSACEUL Ordering and shipping details Category22640 - IEC DISCONNECT-GS1,LK3 Discount ScheduleI11 GTIN00785901546955 Nbr. of units in pkg.1 Package weight(Lbs)19.620000000000001 ReturnabilityN Country of originFR Offer Sustainability RoHS (date code: YYWW)Compliant - since 1545 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest 178 Catalog 08: Operating Mechanisms and Disconnect Switches (Version 1.0)Data BulletinSizeAdd to My DocumentsCADSizeAdd to My DocumentsInstruction SheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.