View all PowerPact L-Frame Molded Case Circuit Breakers
PowerPact L Circuit Breaker,Micrologic3.3,600A,3P,600V,25kAShow more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Main product or component typeCircuit breaker range of productPowerPact L Trip Unit TypeElectronic, standard, Micrologic 3.3, LI Interrupt CodeJ Complementary protection technologyCurrent limiter Line Rated Current600 A Number of Poles3P Interrupt Rating65 kA 480 V AC100 kA 240 V AC25 kA 600 V AC Voltage Rating600 V AC continuous current rating80 % mounting modeUnit mount electrical connectionBusbar connection lineBusbar connection load Terminal TypeAL600LF52K3 height287.02 mm (11.3 in) width139.70 mm (5.5 in) depth167.89 mm (6.61 in) tightening torque38.94…442.54 lbf.in (4.4…50 N.m) 0.15…0.37 in² (95…240 mm²) AWG 3/0...500 kcmil) Environment product certificationsCCCCECSAUL listed Ordering and shipping details Category01116-L ELEC TRIP UNIT MOUNT BREAKER/SW Discount ScheduleDE2 GTIN00785901474906 Package weight(Lbs)15.00 lb(US) (6.804 kg) ReturnabilityYes Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP, which is known to the State of California to cause cancer, and DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm.For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveUnder investigation Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
Documents and DownloadsLanguage
User guideSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction SheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.