LH MOLDED CASE CIRCUIT BREAKER, 600V, 400A, 3PShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main product or component typeCircuit breaker range of productI-Line Trip Unit TypeThermal-magnetic Rating CodeH Complementary Line Rated Current400 A Number of Poles3P Interrupt Rating65 kA at 240 V AC35 kA at 480 V AC25 kA at 600 V AC50 kA at 250 V DC35 kA at 480Y/277 V AC20 kA at 500 V DC25 kA at 600Y/347 V AC System Voltage250 V DC500 V DC600 V AC mounting modeI-Line electrical connectionI-Line connection lineLugs load Wire GaugeAWG 1...600 kcmil (aluminium/copper) 1 cable(s)AWG 1...250 kcmil (aluminium/copper) 2 cable(s) Terminal TypeAL400LA magnetic hold current2000 A magnetic tripping current4000 A height12.5 in width6 in depth4 in Environment product certificationsCSAUL listed Ordering and shipping details Category01040 - LA/LH BRKR, SW, MAG-GARD Discount ScheduleDE2 GTIN00785901339434 Nbr. of units in pkg.1 Package weight(Lbs)18.280000000000001 ReturnabilityY Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1304 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP, which is known to the State of California to cause cancer, and - - - - - - - Substance 2DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsHandoutSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.