PowerPact L Circuit Breaker,Micrologic6.3A,400A,3P,600V,18kAShow more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact L Trip Unit TypeElectronic ammeter Micrologic 6.3 A LSIG Interrupt CodeG Complementary protection technologyCurrent limiter Line Rated Current400 A Number of Poles3P Interrupt Rating65 kA at 240 V AC35 kA at 480 V AC18 kA at 600 V AC System Voltage600 V AC continuous current rating80 % mounting modeUnit mount electrical connectionTerminal nut lineLugs load Wire SizeAWG 2/0...500 kcmil (aluminium/copper) 2(cable(s) Terminal TypeAL600LS52K3 height11.3 in width5.5 in depth6.61 in tightening torque4.4...50 N.m 0.11...0.37 in² (70...240 mm²) AWG 2/0...500 kcmil Environment product certificationsCCCCECSAIECUL listedNMX Ordering and shipping details Category01116 - L ELEC TRIP UNIT MOUNT BREAKER/SW Discount ScheduleDE2 Nbr. of units in pkg.1 Package weight(Lbs)15 ReturnabilityY Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1132 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable
End of Life Information
Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP, which is known to the State of California to cause cancer, and - - - - - - - Substance 2DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.