TeSys SK mini contactor - 3P (3 NO) - AC-3 - 690 V 9 A - 24 V AC coilShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeTeSys product nameTeSys SK product or component typeMini contactor device short nameLC1SKGC contactor applicationMotor controlResistive load utilisation categoryAC-1AC-3 poles description3P pole contact composition3 NO System Voltage690 V AC 50/60 Hz power circuit690 V AC <= 400 Hz signalling circuit [Ie] rated operational current20 A (<= 122 °F (50 °C)) AC AC-19 A at <= 400 V AC AC-3 motor power kW4 kW at 380...415 V AC 50/60 Hz4 kW at 660...690 V AC 50/60 Hz1.1 kW at 220...230 V AC 50/60 Hz control circuit typeAC 50/60 Hz [Uc] control circuit voltage24 V AC 50/60 Hz auxiliary contact composition1 NC [Ith] conventional free air thermal current20 A at <= 131 °F (55 °C) for power circuit10 A at <= 131 °F (55 °C) for signalling circuit Irms rated making capacity85 A AC conforming to NF C 63-11085 A AC conforming to IEC 60947 rated breaking capacity68 A at <= 400 V conforming to NF C 63-11068 A at <= 400 V conforming to IEC 60947 [Icw] rated short-time withstand current60 A <= 131 °F (55 °C) power circuit associated fuse rating20 A gI at <= 440 V for power circuit10 A gI for signalling circuit conforming to IEC 6094710 A gI for signalling circuit conforming to VDE 0660 average impedance4 mOhm at 50 Hz - Ith 20 A for power circuit [Ui] rated insulation voltage690 V for power circuit conforming to CSA C22.2 No 14690 V power circuit conforming to BS 5424690 V power circuit conforming to IEC 60947690 V for power circuit conforming to UL 508690 V for power circuit conforming to VDE 0110 group C mounting supportPanelRail standardsBS 5424IEC 60947NF C 63-110VDE 0660 product certificationscULus connections - terminalsConnector 1 cable(s) 0...0.01 in² (1.5...6 mm²) - cable stiffness: solidConnector 2 cable(s) 0...0.01 in² (1.5...4 mm²) - cable stiffness: solidConnector 1 cable(s) 0...0.01 in² (0.5...6 mm²) - cable stiffness: flexible - without cable endConnector 2 cable(s) 0...0 in² (0.35...2.5 mm²) - cable stiffness: flexible - without cable endConnector 1 cable(s) 0...0.01 in² (0.35...6 mm²) - cable stiffness: flexible - with cable endConnector 2 cable(s) 0...0 in² (0.35...1.5 mm²) - cable stiffness: flexible - with cable end tightening torquePower circuit: 7.08 lbf.in (0.8 N.m) - on connector - with screwdriver pozidriv No 1 operating time6...8 ms coil de-energisation and NO opening7...14 ms coil energisation and NO closing8...16 ms coil energisation and NC opening8...10 ms coil de-energisation and NC closing mechanical durability10 Mcycles operating rate1200 cyc/h Complementary control circuit voltage limits0.85...1.1 Uc at <= 131 °F (55 °C) operational 50/60 Hz0.2...0.75 Uc at <= 131 °F (55 °C) drop-out 50/60 Hz inrush power in VA23 VA at 68 °F (20 °C) 50/60 Hz hold-in power consumption in VA4.9 VA at 68 °F (20 °C) 50/60 Hz heat dissipation1.5 W at 50/60 Hz signalling circuit frequency<= 400 Hz Environment IP degree of protectionIP2x conforming to VDE 0106 protective treatmentTC conforming to IEC 60068TC conforming to DIN 50015 ambient air temperature for operation-4...122 °F (-20...50 °C) ambient air temperature for storage-58...158 °F (-50...70 °C) operating altitude6561.68 ft (2000 m) without derating in temperature height2.28 in (58 mm) width1.77 in (45 mm) depth2.2 in (56 mm) product weight0.39 lb(US) (0.175 kg) Ordering and shipping details Category22326 - CTR,K-LINE,AC,OPEN,NONREV Discount ScheduleI12 GTIN003389110563511 Nbr. of units in pkg.1 Package weight(Lbs)0.37 ReturnabilityN Country of originCZ Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Lead and lead compounds, which is known to the State of California to cause cancer and birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.