TeSys K contactor - 3P - AC-3 <= 440 V 6 A - 1 NC aux. - 24 V AC coilShow more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeTeSys product or component typeContactor product nameTeSys K device short nameLC1K device applicationControl contactor applicationMotor control Complementary utilisation categoryAC-4AC-3 poles description3P power pole contact composition3 NO System Voltage690 V AC 50/60 Hz power circuit<= 690 V AC 50/60 Hz signalling circuit [Ie] rated operational current6 A at <= 440 V AC AC-3 power circuit control circuit typeAC 50/60 Hz [Uc] control circuit voltage24 V AC 50/60 Hz motor power kW1.5 kW at 220...230 V AC 50/60 Hz AC-32.2 kW at 380...415 V AC 50/60 Hz AC-31.5 kW at 400 V AC 50/60 Hz AC-43 kW at 660...690 V AC 50/60 Hz AC-33 kW at 440 V AC 50/60 Hz AC-33 kW at 480 V AC 50/60 Hz AC-33 kW at 500...600 V AC 50/60 Hz AC-3 auxiliary contact composition1 NC [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current20 A at <= 122 °F (50 °C) power circuit10 A at <= 122 °F (50 °C) signalling circuit Irms rated making capacity110 A AC power circuit conforming to NF C 63-110110 A AC power circuit conforming to IEC 60947110 A AC signalling circuit conforming to IEC 60947 rated breaking capacity110 A at 415 V conforming to IEC 60947110 A at 440 V conforming to IEC 6094780 A at 500 V conforming to IEC 60947110 A at 220...230 V conforming to IEC 60947110 A at 380...400 V conforming to IEC 6094770 A at 660...690 V conforming to IEC 60947 [Icw] rated short-time withstand current20 A <= 122 °F (50 °C) >= 15 min power circuit90 A <= 122 °F (50 °C) 1 s power circuit85 A <= 122 °F (50 °C) 5 s power circuit80 A <= 122 °F (50 °C) 10 s power circuit60 A <= 122 °F (50 °C) 30 s power circuit45 A <= 122 °F (50 °C) 1 min power circuit40 A <= 122 °F (50 °C) 3 min power circuit80 A 1 s signalling circuit90 A 500 ms signalling circuit110 A 100 ms signalling circuit associated fuse rating25 A gG at <= 440 V power circuit25 A aM power circuit10 A gG signalling circuit conforming to IEC 6094710 A gG signalling circuit conforming to VDE 0660 average impedance3 mOhm at 50 Hz - Ith 20 A power circuit [Ui] rated insulation voltage690 V signalling circuit conforming to IEC 60947-4-1690 V signalling circuit conforming to IEC 60947-5-1600 V signalling circuit conforming to UL 508600 V power circuit conforming to CSA C22.2 No 14600 V signalling circuit conforming to CSA C22.2 No 14690 V power circuit conforming to IEC 60947-4-1600 V power circuit conforming to UL 508 insulation resistance> 10 MOhm signalling circuit inrush power in VA30 VA at 68 °F (20 °C) hold-in power consumption in VA4.5 VA at 68 °F (20 °C) heat dissipation1.3 W control circuit voltage limits0.2...0.75 Uc at <= 122 °F (50 °C) drop-out0.8...1.15 Uc at <= 122 °F (50 °C) operational connections - terminalsSolder pins 1.5 x 0.9 mm operating rate3600 cyc/h auxiliary contacts typeType instantaneous (1 NC) signalling circuit frequency<= 400 Hz minimum switching current5 mA signalling circuit minimum switching voltage17 V signalling circuit mounting supportPrinted circuit boards operating time10...20 ms coil de-energisation and NO opening10...20 ms coil energisation and NO closing safety reliability levelB10d = 1369863 cycles contactor with nominal load conforming to EN/ISO 13849-1B10d = 20000000 cycles contactor with mechanical load conforming to EN/ISO 13849-1 non overlap distance0.02 in (0.5 mm) mechanical durability10 Mcycles electrical durability1.3 Mcycles 6 A AC-3 at Ue <= 440 V mechanical robustnessShocks contactor closed, on X axis 10 Gn for 11 ms IEC 60068-2-27Shocks contactor closed, on Y axis 15 Gn for 11 ms IEC 60068-2-27Shocks contactor closed, on Z axis 15 Gn for 11 ms IEC 60068-2-27Shocks contactor opened, on X axis 6 Gn for 11 ms IEC 60068-2-27Shocks contactor opened, on Y axis 10 Gn for 11 ms IEC 60068-2-27Shocks contactor opened, on Z axis 10 Gn for 11 ms IEC 60068-2-27Vibrations contactor closed 4 Gn, 5...300 Hz IEC 60068-2-6Vibrations contactor opened 2 Gn, 5...300 Hz IEC 60068-2-6 height2.28 in (58 mm) width1.77 in (45 mm) depth2.24 in (57 mm) product weight0.4 lb(US) (0.18 kg) Environment standardsBS 5424IEC 60947NF C 63-110VDE 0660 product certificationsCSAUL IP degree of protectionIP2x conforming to VDE 0106 protective treatmentTC conforming to IEC 60068TC conforming to DIN 50016 ambient air temperature for operation-13...122 °F (-25...50 °C) ambient air temperature for storage-58...176 °F (-50...80 °C) operating altitude6561.68 ft (2000 m) without derating flame retardanceV1 conforming to UL 94Requirement 2 conforming to NF F 16-101Requirement 2 conforming to NF F 16-102 Ordering and shipping details Category22326 - CTR,K-LINE,AC,OPEN,NONREV Discount ScheduleI12 GTIN003389110488159 Nbr. of units in pkg.1 Package weight(Lbs)0.46000000000000002 ReturnabilityN Country of originFR Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0633 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Antimony oxide & Antimony trioxide, which is known to the State of California to cause cancer. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
Data BulletinSizeAdd to My DocumentsCADSizeAdd to My DocumentsIEC Contactor, 6-12A, 3 Pole, K-Line, Solder Pin Terminals (Version 1.2)CAD for LC1K06015B7: TeSys K contactor - 3P - AC-3 <= 440 V 6 A - 1 NC aux. - 24 V AC coil (Version 1.0)CertificateSizeAdd to My DocumentsInstruction SheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.