View all TeSys Integral 18, 32, 63
TeSys integral - protection module - AC-43 - magnetic - 240...480 AShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeTeSys device short nameLB6LD range compatibilityTeSys Integral contactor breaker product or component typeProtection module poles description3P utilisation categoryAC-43 [Ue] rated operational voltage690 V AC magnetic tripping current240…480 A trip unit technologyMagnetic protection typePhase imbalance Complementary motor power kW9 kW 220...240 V AC 50/60 Hz22 kW 400...415 V AC 50/60 Hz22 kW 440 V AC 50/60 Hz25 kW 480...525 V AC 50/60 Hz33 kW 600...690 V AC 50/60 Hz net weight1.72 lb(US) (0.78 kg) Environment standardsNF C 63-650 protective treatmentTH IP degree of protectionIP20 B IEC 60144IP20 B IEC 60529 ambient air temperature for operation-4…140 °F (-20…60 °C) Ordering and shipping details Category22384 - STARTERS,INTEGRAL,ACCESS Discount ScheduleI11 GTIN00785901256892 Package weight(Lbs)1.09 kg (2.41 lb(US)) ReturnabilityNo Country of originFR Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: No which is known to the State of California to cause No harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveUnder investigation Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins. Contractual warranty Warranty18 months
CatalogSizeAdd to My DocumentsCADSizeAdd to My DocumentsAdd-on\Protection module (Version 1.0)Product Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.