FA/LA MOLDED CASE CIRCUIT BREAKER, 600V, 300A, 3P, I-Line, SHORT HANDLEShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main product or component typeCircuit breaker range of productI-Line Trip Unit TypeMagnetic Rating CodeA OptionsHandle Complementary Line Rated Current300 A Number of Poles3P Interrupt Rating42 kA at 240 V AC30 kA at 480 V AC22 kA at 600 V AC10 kA at 125 V DC10 kA at 250 V DC42 kA at 120 V AC30 kA at 480Y/277 V AC System Voltage600 V AC mounting modeUnit mount electrical connectionTerminal lineLugs load Wire GaugeAWG 1...600 kcmil (aluminium/copper) 1 cable(s)AWG 1...250 kcmil (aluminium/copper) 2 cable(s) Terminal TypeAL400LA magnetic hold current1500 A magnetic tripping current3000 A operator profileShort lever wiring configuration3-wire height11 in width6 in depth5.84 in Environment product certificationsCSAIECUL listed Ordering and shipping details Category00935 - LAL/LHL BRKR, SW, MAG-GARD Discount ScheduleDE2 GTIN00785901530060 Nbr. of units in pkg.1 Package weight(Lbs)15.800000000000001 ReturnabilityY Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP, which is known to the State of California to cause cancer, and - - - - - - - Substance 2DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction SheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.