View all TeSys F Contactors
TeSys D - auxiliary contact block - 2 NC - screw-clamps terminalsShow more characteristics >
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main range of productTeSys DTeSys FTeSys D control relay rangeTeSys product or component typeAuxiliary contact block auxiliary contacts operationInstantaneous pole contact composition2 NC connections - terminalsscrew clamp terminals 1 0.00…0.00 in² (1…2.5 mm²)flexible with cable end screw clamp terminals 1 0.00…0.00 in² (1…2.5 mm²)flexible without cable end screw clamp terminals 2 0.00…0.00 in² (1…2.5 mm²)flexible with cable end screw clamp terminals 2 0.00…0.00 in² (1…2.5 mm²)flexible without cable end screw clamp terminals 1 0.00…0.00 in² (1…2.5 mm²)solid with cable end screw clamp terminals 1 0.00…0.00 in² (1…2.5 mm²)solid without cable end screw clamp terminals 2 0.00…0.00 in² (1…2.5 mm²)solid with cable end screw clamp terminals 2 0.00…0.00 in² (1…2.5 mm²)solid without cable end Complementary mounting locationFront [Ui] rated insulation voltage600 V UL690 V IEC 60947-5-1600 V CSA [Ue] rated operational voltage690 V AC 25...400 Hz [Ith] conventional free air thermal current10 A 140 °F (60 °C) Irms rated making capacity140 A <= 690 V AC IEC 60947-5-1250 A <= 690 V DC IEC 60947-5-1 permissible short-time rating100 A 140 °F (60 °C) 1 s120 A 140 °F (60 °C) 500 ms140 A 140 °F (60 °C) 100 ms protection typeGG fuse 10 A rating according to operational current for Ue <= 690 V associated fuse rating10 A gG IEC 60947-5-1 mechanical durability30 Mcycles minimum switching current5 mA minimum switching voltage17 V non-overlap time1.5 ms on de-energisation no overlap between NC and NO contact1.5 ms on energisation no overlap between NC and NO contact overlap time1.5 ms insulation resistance> 10 MOhm Environment environmental characteristicNormal environment standardsBS 4794NF C 63-140EN 60947-5-1VDE 0660IEC 60947-5-1 product certificationsULCSA IP degree of protectionIP2x VDE 0106 protective treatmentTH IEC 60068 ambient air temperature for operation23…140 °F (-5…60 °C) ambient air temperature for storage-76…176 °F (-60…80 °C) operating altitude9842.52 ft (3000 m) without Ordering and shipping details Category22341 - CONTACTOR,D,K,&F ACCESS Discount ScheduleI12 GTIN00785901213642 Package weight(Lbs)0.04 kg (0.08 lb(US)) ReturnabilityYes Country of originFR Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins. Contractual warranty Warranty18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest 178 Catalog 18: Contactors and Starters-IEC (Version 1.0)Digest 178 Catalog 16: NEMA and Definite Purpose Contactors and Starters (Version 1.0)Digest 178 Catalog 23: Relays and Timers (Version 1.0)Control Panel Technical Guide - How to quickly design optimized contactor assemblies (Version 1.1)TeSys catalogue - 2019 - 2020 - chapter B9 high power contactors TeSys F,V, FG, CR1F (Version 7.0)Tesys catalogue 2019 - 2020 Motor control and protection components (Version 9.2)TeSys catalogue - 2019 - 2020 - chapter B8 contactors TeSys SK,K, D, SKGC, GC, GY,GF (Version 7.0)CADSizeAdd to My DocumentsCAD file (on TraceParts) for LADN02: TeSys D - auxiliary contact block - 2 NC - screw-clamps terminals (Version 3.0)CAD for LADN02: TeSys D - auxiliary contact block - 2 NC - screw-clamps terminals (Version 1.0)CONTACTS BLOCK (Version 1.0)
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.