PowerPact H Circuit Breaker,ThermMagn,15A,2P,600V,14kAShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact H Trip Unit TypeThermal-magnetic breaking capacity codeD Complementary Line Rated Current15 A Number of Poles2P Interrupt Rating18 kA at 480 V AC25 kA at 240 V AC14 kA at 600 V AC20 kA at 250 V DC System Voltage250 V DC600 V AC continuous current rating80 % mounting modeUnit mount electrical connectionBusbar connection loadBusbar connection line magnetic hold current350 A magnetic tripping current750 A height6.4 in width2.74 in depth4.36 in tightening torque5 N.m for 2.5...95 mm² (AWG 14...AWG 3/0) Environment product certificationsCSAUL listedCECCCIEC ambient air temperature for operation104 °F (40 °C) Ordering and shipping details Category01110 - HD,JD UNIT MT BREAKER/SWITCH Discount ScheduleDE2 GTIN00785901180111 Nbr. of units in pkg.1 Package weight(Lbs)3 ReturnabilityY Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0832 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP, which is known to the State of California to cause cancer, and - - - - - - - Substance 2DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsData BulletinSizeAdd to My DocumentsCADSizeAdd to My DocumentsBrochureSizeAdd to My DocumentsSpecification guideSizeAdd to My DocumentsCertificateSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.