TeSys GV2-Circuit breaker-thermal-magnetic - 4...6.3 A - screw clamp terminalsShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main rangeTeSys product nameTeSys GV2 device short nameGV2ME product or component typeCircuit breaker device applicationMotor trip unit technologyThermal-magnetic Complementary poles description3P network typeAC utilisation categoryAC-3 conforming to IEC 60947-4-1Category A conforming to IEC 60947-2 network frequency50/60 Hz conforming to IEC 60947-4-1 fixing modeClipped on 35 mm symmetrical DIN railScrewed on panel (with adaptor plate) operating positionAny position motor power kW3 kW at 500 V AC 50/60 Hz4 kW at 690 V AC 50/60 Hz2.2 kW at 400/415 V AC 50/60 Hz breaking capacity3 kA Icu at 690 V AC 50/60 Hz conforming to IEC 60947-250 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-250 kA Icu at 500 V AC 50/60 Hz conforming to IEC 60947-2100 kA Icu at 230/240 V AC 50/60 Hz conforming to IEC 60947-2100 kA Icu at 400/415 V AC 50/60 Hz conforming to IEC 60947-2 [Ics] rated service short-circuit breaking capacity100 % at 230/240 V AC 50/60 Hz conforming to IEC 60947-2100 % at 440 V AC 50/60 Hz conforming to IEC 60947-2100 % at 500 V AC 50/60 Hz conforming to IEC 60947-275 %at 690 V AC 50/60 Hz conforming to IEC 60947-2100 % at 400/415 V AC 50/60 Hz conforming to IEC 60947-2 control typePush-button [In] rated current6.3 A thermal protection adjustment range4...6.3 A magnetic tripping current78 A System Voltage690 V AC 50/60 Hz conforming to IEC 60947-2 [Ui] rated insulation voltage690 V AC 50/60 Hz conforming to IEC 60947-2 [Ith] conventional free air thermal current6.3 A conforming to IEC 60947-4-1 [Uimp] rated impulse withstand voltage6 kV conforming to IEC 60947-2 power dissipation per pole2.5 W mechanical durability100000 cycles electrical durability100000 cycles AC-3 at 440 V operating rate25 cyc/h rated dutyContinuous conforming to IEC 60947-4-1 connections - terminalsScrew clamp terminals 2 cable(s) 1...6 mm² solidScrew clamp terminals 2 cable(s) 1.5...6 mm² flexible without cable endScrew clamp terminals 2 cable(s) 1...4 mm² flexible with cable end tightening torque1.7 N.m on screw clamp terminals suitability for isolationYes conforming to IEC 60947-1 phase failure sensitivityYes conforming to IEC 60947-4-1 height3.5 in (89 mm) width1.77 in (45 mm) depth3.08 in (78.2 mm) product weight0.57 lb(US) (0.26 kg) Environment standardsEN 60204IEC 60947-1IEC 60947-2IEC 60947-4-1NF C 63-120NF C 63-650NF C 79-130UL 508VDE 0113VDE 0660CSA C22.2 product certificationsATEXBVCCCCEBECCSADNVEZUGLLROS (Lloyds register of shipping)RINASETITSEULEAC protective treatmentTH IP degree of protectionIP20 conforming to IEC 60529 IK degree of protectionIK04 ambient air temperature for operation-4...140 °F (-20...60 °C) ambient air temperature for storage-40...176 °F (-40...80 °C) fire resistance1760 °F (960 °C) conforming to IEC 60695-2-1 operating altitude6561.68 ft (2000 m) Ordering and shipping details Category22367 - MANUAL STR PROTECTOR - GV2 Discount ScheduleI11 GTIN00785901211969 Nbr. of units in pkg.1 Package weight(Lbs)0.62 ReturnabilityY Country of originTH Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Antimony oxide & Antimony trioxide, which is known to the State of California to cause cancer. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsCADSizeAdd to My DocumentsThermal-magnetic circuit-breaker GV2ME for connection by screw clamp terminals.Thermal magnetic motor circuit-breaker\Pushbutton controlmotor circuit-breaker 25 AGV2ME MOTOR CB THER/MAG ROCKER
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.