View all TeSys F Contactors
View all TeSys F Contactors
TeSys F magnetic latching contactor - 3P(3 NO) - 500 A - 220...230 V AC/DC coilShow more characteristics >
CR1F500M7 has not been replaced. Please contact your customer care center for more information.
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
- Price*7,752.00 USD
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeTeSys product nameTeSys F product or component typeMagnetic latching contactor device short nameCR1F device applicationControl contactor applicationResistive loadMotor control utilisation categoryAC-3AC-1AC-4 poles description3P power pole contact composition3 NO System Voltage1000 V AC 25...200 Hz [Ie] rated operational current700 A (<= 104 °F (40 °C)) at <= 440 V AC AC-1500 A (<= 104 °F (40 °C)) at <= 440 V AC AC-3460 A (<= 104 °F (40 °C)) at <= 440 V AC AC-4 motor power kW250 kW at 400 V AC 50/60 Hz AC-4 control circuit typeAC 50...400 HzDC standard [Uc] control circuit voltage220...230 V AC 50...400 Hz220...230 V DC Irms rated making capacity5000 A rated breaking capacity5000 A at 220...440 V4500 A at 500 V2500 A at 1000 V3560 A at 660/690 V [Icw] rated short-time withstand current4200 A <= 104 °F (40 °C) 10 s3200 A <= 104 °F (40 °C) 30 s2400 A <= 104 °F (40 °C) 1 min1500 A <= 104 °F (40 °C) 3 min1200 A <= 104 °F (40 °C) 10 min4200 A <= 104 °F (40 °C) 1 s4200 A <= 104 °F (40 °C) 5 s associated fuse rating500 A aM at <= 440 V800 A gG at <= 440 V800 A BS88 at <= 440 V average impedance0.18 mOhm at 50 Hz - Ith 700 A [Ui] rated insulation voltage1500 V conforming to VDE 0110 group C1000 V conforming to IEC 60158-11000 V conforming to IEC 60947-41000 V conforming to BS 775 power dissipation per pole45 W AC-388 W AC-1 connections - terminalsLugs-ring terminals 2 cable(s) 0.37 in² (240 mm²)Bars 2 x (40 x 5 mm)Power circuit: bolted connection tightening torque309.73 lbf.in (35 N.m) operating time50...100 ms unlatching40...80 ms latching mechanical durability1 Mcycles operating rate120 cyc/h at <= 104 °F (40 °C) Complementary control circuit voltage limits0.85...1.1 Uc latching0.85...1.1 Uc unlatching average consumption1800 VA AC 50...400 Hz latching1800 VA DC latching13 VA AC 50...400 Hz unlatching13 VA DC unlatching Environment protective treatmentTC ambient air temperature for operation5...158 °F (-15...70 °C) ambient air temperature for storage-76...176 °F (-60...80 °C) operating altitude9842.52 ft (3000 m) without derating height9.37 in (238 mm) width9.17 in (233 mm) depth9.13 in (232 mm) product weight24.91 lb(US) (11.3 kg) Ordering and shipping details Category22336 - CTR,F-LINE,AC,OPEN,NONREV Discount ScheduleI12 Nbr. of units in pkg.1 Package weight(Lbs)26.370000000000001 ReturnabilityN Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0915 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Lead and lead compounds, which is known to the State of California to cause cancer and birth defects or other reproductive harm. - - - - - - - Substance 2Bisphenol A (BPA), which is known to the State of California to cause birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsTeSys catalogue - 2019 - 2020 - chapter B9 high power contactors TeSys F,V, FG, CR1F (Version 7.0)Control Panel Technical Guide - How to quickly design optimized contactor assemblies (Version 1.1)CADSizeAdd to My DocumentsCAD file (on TraceParts) for CR1F500M7: TeSys F magnetic latching contactor - 3P(3 NO) - 500 A - 220...230 V AC/DC coil (Version 2.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.