TeSys K control relay - 4 NO - <= 690 V - 42 V AC coilShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangeTeSys product nameTeSys CAK product or component typeControl relay device short nameCA2K contactor applicationControl circuit utilisation categoryAC-15DC-13 pole contact composition4 NO System Voltage<= 690 V <= 400 Hz control circuit typeAC 50/60 Hz [Uc] control circuit voltage42 V AC 50/60 Hz Complementary [Ith] conventional free air thermal current10 A at <= 122 °F (50 °C) Irms rated making capacity110 A conforming to IEC 60947 associated fuse rating10 A gG conforming to IEC 6094710 A gG conforming to VDE 0660 [Ui] rated insulation voltage600 V conforming to CSA C22.2 No 14690 V conforming to BS 5424690 V conforming to IEC 60947750 V conforming to VDE 0110 group C mounting supportPlateRail connections - terminalsScrew clamp terminals 1 cable(s) 0...0.01 in² (1.5...4 mm²) - cable stiffness: solidScrew clamp terminals 2 cable(s) 0...0.01 in² (1.5...4 mm²) - cable stiffness: solidScrew clamp terminals 2 cable(s) 0...0.01 in² (0.75...4 mm²) - cable stiffness: flexible - without cable endScrew clamp terminals 1 cable(s) 0...0.01 in² (0.75...4 mm²) - cable stiffness: flexible - with cable endScrew clamp terminals 1 cable(s) 0...0 in² (0.34...1.5 mm²) - cable stiffness: flexible - with cable endScrew clamp terminals 2 cable(s) 0...0 in² (0.34...1.5 mm²) - cable stiffness: flexible - without cable end tightening torque11.5 lbf.in (1.3 N.m) - on screw clamp terminals - with screwdriver Philips No 2 0.24 in (6 mm)11.5 lbf.in (1.3 N.m) - on screw clamp terminals - with screwdriver flat Ø 6 mm control circuit voltage limits0.8...1.15 Uc at 122 °F (50 °C) operational0.2...0.75 Uc at 122 °F (50 °C) drop-out operating time10...20 ms coil de-energisation and NO opening10...20 ms coil energisation and NO closing mechanical durability10 Mcycles operating rate10000 cyc/h immunity to microbreaks2 ms inrush power in VA30 VA at 68 °F (20 °C) hold-in power consumption in VA4.5 VA at 68 °F (20 °C) heat dissipation1.3 W minimum switching voltage17 V minimum switching current5 mA non overlap distance0.02 in (0.5 mm) insulation resistance> 10 MOhm height2.28 in (58 mm) width1.77 in (45 mm) depth2.24 in (57 mm) product weight0.4 lb(US) (0.18 kg) Environment standardsBS 5424IEC 60947VDE 0660NF C 63-140 product certificationsCSAUL IP degree of protectionIP2x protective treatmentTC conforming to IEC 60068 ambient air temperature for operation-13...122 °F (-25...50 °C) ambient air temperature for storage-58...176 °F (-50...80 °C) operating altitude6561.68 ft (2000 m) without derating flame retardanceV1 conforming to UL 94Requirement 2 conforming to NF F 16-101Requirement 2 conforming to NF F 16-102 mechanical robustnessVibrations contactor closed 4 Gn, 5...300 Hz IEC 60068-2-6Vibrations contactor open 2 Gn, 5...300 Hz IEC 60068-2-6Shocks contactor open 10 Gn for 11 ms IEC 60068-2-27Shocks contactor closed 15 Gn for 11 ms IEC 60068-2-27 Ordering and shipping details Category22371 - RELAYS, CONTROL Discount ScheduleI12 GTIN003389110482959 Nbr. of units in pkg.1 Package weight(Lbs)0.41000000000000003 ReturnabilityN Country of originFR Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Antimony oxide & Antimony trioxide, which is known to the State of California to cause cancer. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsCADSizeAdd to My DocumentsIEC Industrial Control Relay (K-Line), CA2KN, CA3KN, CA4KN (Version 1.2)CAD for CA2KN40D7: TeSys K control relay - 4 NO - <= 690 V - 42 V AC coil (Version 1.0)Instruction SheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.