PowerPact - automatic switch - 600V 125A 2P - ElinkShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangePowerPact product namePowerPact B product or component typeAutomatic switch device applicationDistribution Complementary Line Rated Current125 A Number of Poles2P control typeToggle breaking capacity codeJ breaking capacity65 kA at 480 V AC25 kA at 600 V AC100 kA at 240 V AC65 kA at 480Y/277 V AC100 kA at 208Y/120 V AC System Voltage600Y/347 V AC 50/60 Hz UL 489 magnetic hold current880 A magnetic tripping current1320 A Mechanical durability15000 cycles according to IEC 947-1 Annex K ed 5.2 Electrical durability10000 cycles according to IEC 947-1 Annex K ed 5.2 at 440 V In contact position indicatorYes connection pitch1.06 in (27 mm) local signallingGreen flag presence of auxiliary contacts mounting modeBy screws plateClip-on 35 x 15 mm symmetrical DIN rail electrical connectionEverlink lug at lineEverlink lug at load AWG gaugeAWG 6...AWG 2/0 fine stranded (aluminium/copper)AWG 14...AWG 3/0 rigid or stranded (aluminium/copper) tightening torque44.25 lbf.in (5 N.m) 0...0.02 in² (2.5...10 mm²)79.65 lbf.in (9 N.m) 0.02...0.15 in² (16...95 mm²) number of slots1 auxiliary switch OF (plug-in)1 voltage release MN or MX (plug-in) Power wire stripping length0.79 in (20 mm) ColorGrey (RAL 7016) 9 mm pitches6 height5.39 in (137 mm) width1.42 in (36 mm) depth3.5 in (89 mm) quantity per setSet of 1 Environment quality labelsCE standardsUL 489 product certificationsUL ambient air temperature for operation-13...158 °F (-25...70 °C) ambient air temperature for storage-58...185 °F (-50...85 °C) operating altitude5000 m with derating6561.68 ft (2000 m) without derating Ordering and shipping details Category01132 - BJ/BK UNIT MOUNT BREAKER/SWITCH Discount ScheduleDE2 Nbr. of units in pkg.1 Package weight(Lbs)2.0899999999999999 ReturnabilityY Country of originUS
Documents and DownloadsLanguage
CertificateSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.