PowerPact - circuit breaker - 80A 4P AC 18kA at 480/440 (UL) - EverLink lugShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangePowerPact product namePowerPact B device short nameBD 080 product or component typeCircuit breaker device applicationDistribution Complementary Line Rated Current80 A Number of Poles4P protected poles description4t control typeToggle breaking capacity codeD breaking capacity25 kA at 240 V AC 50/60 Hz according to UL 48918 kA at 480 V AC 50/60 Hz according to UL 489Icu: 25 kA at 220...240 V AC 50/60 Hz according to IEC 60947-2Icu: 18 kA at 380...415 V AC 50/60 Hz according to IEC 60947-2Icu: 14 kA at 500...525 V AC 50/60 Hz according to IEC 60947-218 kA at 480Y/277 V AC 50/60 Hz according to UL 48925 kA at 208Y/120 V AC 50/60 Hz according to UL 489 System Voltage600Y/347 V AC 50/60 Hz according to UL 489500/525 V AC 50/60 Hz according to IEC 60947-2 [Ics] rated service breaking capacity25 kA: at 220...240 V AC 50/60 Hz according to IEC 60947-218 kA: at 380...415 V AC 50/60 Hz according to IEC 60947-218 kA: at 440 V AC 50/60 Hz according to IEC 60947-214 kA: at 500...525 V AC 50/60 Hz according to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV according to IEC 60947-2 [Ui] rated insulation voltage800 V according to IEC 60947-2 trip unit technologyThermal-magnetic trip unit nameTM-D suitability for isolationYes according to IEC 60947-2 utilisation categoryCategory A Mechanical durability20000 cycles according to IEC 947-1 Annex K ed 5.2 Electrical durability10000 cycles according to IEC 947-1 Annex K ed 5.2 In at 440 V connection pitch1.06 in (27 mm) local signallingGreen flag presence of auxiliary contacts mounting modeBy screws plateClip-on 35 x 15 mm symmetrical DIN rail electrical connectionEverlink lug at lineEverlink lug at load AWG gaugeAWG 6...AWG 2/0 fine stranded (aluminium/copper)AWG 14...AWG 3/0 rigid or stranded (aluminium/copper) tightening torque44.25 lbf.in (5 N.m) 0...0.02 in² (2.5...16 mm²) (AWG 14...AWG 4)79.65 lbf.in (9 N.m) 0.04...0.15 in² (25...95 mm²) (AWG 3...AWG 3/0) number of slots1 auxiliary switch OF (plug-in)1 voltage release MN or MX (plug-in)1 alarm switch SD (plug-in) Power wire stripping length0.79 in (20 mm) ColorGrey (RAL 7016) 9 mm pitches12 height5.39 in (137 mm) width4.25 in (108 mm) depth3.15 in (80 mm) product weight3.18 lb(US) (1.441 kg) quantity per setSet of 1 continuous current rating80 % Environment quality labelsCE standardsEN/IEC 60947-2EN/IEC 60947-5-1GB 14048.2NEMA AB1UL 489CSA C22.2 No 5NMX J-266 product certificationsULCSACCCEACNOMIEC IP degree of protectionIP40 (front cover) according to IEC 60529 IK degree of protectionIK07 according to IEC 62262 pollution degree3 according to IEC 60947-1 ambient air temperature for operation-13...158 °F (-25...70 °C) ambient air temperature for storage-58...185 °F (-50...85 °C) operating altitudeWith deratingWithout derating Ordering and shipping details Category01130 - BD UNIT MOUNT BREAKER/SWITCH Discount ScheduleDE2 GTIN003606489863791 Nbr. of units in pkg.1 Package weight(Lbs)2.6000000000000001 ReturnabilityN Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1DINP, which is known to the State of California to cause cancer, and - - - - - - - Substance 2DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsPowerPact B-Frame 15 to 125 A Circuit Breakers - Catalog (Version 2.0)CertificateSizeAdd to My DocumentsInstruction SheetSizeAdd to My DocumentsTripping curvesSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.