BCPM power monitoring intermediate - 84 solid core 100 A - 26 mm CT spacingShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangePowerLogic product namePowerLogic BCPM product or component typeMulti-circuit energy meter device short nameBCPMB variantIntermediate power monitoringBasic instrumentation energy managementSub billing and cost allocation device applicationSub billing power quality analysisVoltage sag and swell detection type of measurementVoltageCurrentFrequencyActive powerPower factorActive energy [Us] rated supply voltage90...277 V, AC, 50/60 Hz +/- 1 % network frequency50 Hz60 Hz Complementary analogue input typeSolid core CT, 100 A x 84 update time1.8 s measurement voltage90...277 V phase to neutral150...480 V phase to phase measurement accuracy2 % branch current 0.25…2 A1 % branch current 2…100 A3 % mains current 1…100 %3 % mains current 2…100 %1 % voltage 90…277 V sampling rate256 samples/cycle connection pitch1.02 in (26 mm) provided equipment84 x current transformer4 x cables communication port protocolModbus RTU communication port supportRS485 communication of dataOver voltage alarmUnder voltage alarmHigh-high current alarmHigh current alarmLow current alarmLow-low current alarm Environment mounting modePanel-mounted mounting supportEnclosurePanel relative humidity95 % between 32...140 °F (0...60 °C) ambient air temperature for storage-40...158 °F (-40...70 °C) operating altitude9842.52 ft (3000 m) standardsEN 61010IEC 61036UL 508ANSI C12.1 product certificationsUL width11.34 in (288 mm) height5.75 in (146 mm) product weight3.31 lb(US) (1.5 kg) Ordering and shipping details Category09793 - PLOGIC BRANCH CIRCUIT BCPM & MCM Discount SchedulePL1 GTIN003606480299568 Nbr. of units in pkg.1 Package weight(Lbs)7 ReturnabilityN Country of originUS Offer Sustainability RoHS (date code: YYWW) California proposition 65WARNING: Cancer and Reproductive Harm - www.P65Warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.