Overview DescriptionThe Rack Air Distribution Unit is a 2U fan unit that connects into the raised floor and pulls supply air directly into the enclosure. This prevents the conditioned air from mixing with warmer room air before reaching the equipment. This minimizes temperature differences between the top and bottom of the enclosure, while also preventing hot exhaust air recirculation to the inlet of the enclosure. The product is recommended for rack enclosures with loads greater than 1.5kW and can provide airflow for loads up to 3.5kW. It is also ideal for enclosures in raised floor environments where underfloor air distribution is inadequate. Model NameRack Air Distribution Unit 2U 120V 60HZ IncludesRack Mounting brackets , User Manual Standard Lead TimeUsually in Stock Product DistributionAnguilla , Antigua And Barbuda , Aruba , Barbados , Belize , Bermuda , Bolivia , Brazil , Canada , Colombia , Costa Rica , Cuba , Dominican Republic , Ecuador , El Salvador , Falkland Islands (Malvinas) , Guatemala , Guyana , Honduras , Jamaica , Mexico , Netherlands Antilles , Nicaragua , Panama , Peru , Puerto Rico , Taiwan , Trinidad And Tobago , United States , Venezuela , VIRGIN ISLANDS (UNITED STATES) General Refrigerant Charge0.0 Air Flow503.0 Amp Draw In-Rush0 Condensate Pump Capacity0.0 Input Number of Power Cords2 Nominal Input Voltage120V Input Power240 W Input Frequency60 Hz +/- 1Hz Rack Height2 U Input ConnectionsC-13 , NEMA 5-15P Communications & Management Available SmartSlot™ Interface Quantity0 Physical Maximum Height3.5 inches (89.0 mm) Maximum Width16.61 inches (422.0 mm) Maximum Depth29.0 inches (737.0 mm) Net Weight41.0 lbs (18.64 kg) Shipping Weight59.0 lbs (26.82 kg) Shipping Height10.0 inches (254.0 mm) Shipping Width33.0 inches (838.0 mm) Shipping Depth33.0 inches (838.0 mm) ColorBlack Units per Pallet0.0 Conformance ApprovalsUL Recognized Standard warranty2 years repair or replace
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsCertificateSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.