Advantys Telefast ABE 7 - ABE7H12R50
Interfaces for PLCs
passive connection sub-base ABE7 - 12 inputs or outputsShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
- Price129.00 USD
Main range of productAdvantys Telefast ABE7 product or component typePassive discrete I/O sub-base sub-base typeI/O sub-base [Us] rated supply voltage19...30 V conforming to IEC 61131-2 number of channels12 number of terminal per channel1 connections - terminalsScrew type terminals, clamping capacity: 1 x 0.09...1 x 1.5 mm² AWG 28...AWG 16 flexible with cable endScrew type terminals, clamping capacity: 1 x 0.14...1 x 2.5 mm² AWG 26...AWG 12 solidScrew type terminals, clamping capacity: 1 x 0.14...1 x 2.5 mm² AWG 26...AWG 14 flexible without cable endScrew type terminals, clamping capacity: 2 x 0.09...2 x 0.75 mm² AWG 28...AWG 20 flexible with cable endScrew type terminals, clamping capacity: 2 x 0.2...2 x 2.5 mm² AWG 24...AWG 14 solid Complementary supply circuit typeDC number of horizontal rows2 status LED1 LED, green power ON polarity distributionNo short-circuit protection6.3 A internal fuse, 5 x 20 mm, fast blow (PLC end) connector typeHE-10 pin number20 pins fixing modeBy clips on 35 mm symmetrical DIN railBy screws on solid plate with fixing kit supply current<= 6.1 A current per channel<= 0.5 A current per output common<= 6.1 A voltage drop on power supply fuse0.2 V [Ui] rated insulation voltage2000 V installation categoryII conforming to IEC 60664-1 tightening torque5.31 lbf.in (0.6 N.m) (with flat Ø 3.5 mm) width3.31 in (84 mm) product weight0.43 lb(US) (0.196 kg) Environment product certificationsBVCSADNVGLLROS (Lloyds register of shipping)UL IP degree of protectionIP2x conforming to IEC 60529 resistance to incandescent wire1382 °F (750 °C) conforming to IEC 60695-2-11 shock resistance15 gn 11 ms conforming to IEC 60068-2-27 vibration resistance2 gn (f = 10...150 Hz) conforming to IEC 60068-2-6 resistance to electrostatic discharge4 kV (contact) conforming to IEC 61000-4-2 level 38 kV (air) conforming to IEC 61000-4-2 level 3 resistance to radiated fields9.14 V/yd (10 V/m) (26000000...1000000000 Hz) conforming to IEC 61000-4-3 level 3 resistance to fast transients2 kV conforming to IEC 61000-4-4 level 3 ambient air temperature for operation23...140 °F (-5...60 °C) conforming to IEC 61131-2 ambient air temperature for storage-40...176 °F (-40...80 °C) conforming to IEC 61131-2 pollution degree2 conforming to IEC 60664-1 Ordering and shipping details Category22375 - INTERFACE MODULE(ABA,R,S) Discount ScheduleCP2 GTIN00785901285816 Nbr. of units in pkg.1 Package weight(Lbs)0.47999999999999998 ReturnabilityN Country of originFR Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Lead and lead compounds, which is known to the State of California to cause cancer and birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsPremium automation platform - Telefast 2 - Sub-bases
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Dimensions DrawingsDimensions(1)ABE7BV10 / ABE7BV10E
Mounting and ClearanceMounting
Connections and SchemaHE10 12 ChannelsWiring Diagrams(1)Inductive load
Performance CurvesCurves for Determining Cable Type and Length According to the Current12-channel Sub-baseLCable lengthITTotal current per sub base (A)IAAverage current per channel (mA)(1)TSXCDP••2 and ABFH20H••0 cables with c.s.a. 0.08 mm2 (AWG 28).(2)TSXCDP••3 cables with c.s.a. 0.34 mm2 (AWG 22).(3)Cables with c.s.a. 0.13 mm2 (AWG 26).
The curves are given for a voltage drop of 1 V in the cable. For n volts tolerance, multiply the length determined from the graph by n.