Power Distribution Block 3 Pole 2 Line 8 Load 600V 760A CU / 600V 620A ALShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main Range9080LB ProductPower Distribution Block Current Rating760 A for copper cable(s)620 A for aluminium cable(s) Complementary System Voltage600 V AC/DC Mounting TypeSurface mount number of poles3 Terminals per Pole2 line8 load Wire Size2 cable(s) AWG 4...500 kcmil (copper or aluminium) for line8 cable(s) AWG 14...AWG 2/0 (copper or aluminium) for load Electrical ConnectionTin plated aluminium lugs SCCRUp to 100 kA per UL 508 A ambient air temperature for operation-40...302 °F Block MaterialPhenolic block Terminal Tightening TorqueLug 40 lbf.in for AWG 8 (copper or aluminium) loadLug 120 lbf.in for AWG 6...AWG 2/0 (copper or aluminium) loadLug 35 lbf.in for AWG 14...AWG 10 (copper or aluminium) loadLug 375 lbf.in for AWG 4...500 kcmil (copper or aluminium) line wire stripping length0.75 in top load connection1.13 in line connection1.38 in bottom load connection height5.5 in width8.54 in depth3.13 in End Barrier9080LB53 Environment CertificationsCECSA file 70361 class 6228 01UL recognized E60616 CCN XCFR2 Ordering and shipping details Category21711 - 9080 LB Discount ScheduleCP1 GTIN00785901097563 Nbr. of units in pkg.1 Package weight(Lbs)3.6600000000000001 ReturnabilityY Country of originUS Offer Sustainability RoHS (date code: YYWW) REACh California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Lead and lead compounds, which is known to the State of California to cause cancer and birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDigest Catalog 24: Terminal Blocks (Version 1.8)CADSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.