Power Distribution Block 3 Pole 1 Line 4 Load 600V 335A CU / 600V 270A ALShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main Range9080LB ProductPower Distribution Block Current Rating335 A for copper cable(s)270 A for aluminium cable(s) Short Circuit Current Rating65 kA Complementary System Voltage600 V AC/DC Mounting TypeSurface mount number of poles3 Terminals per Pole1 line4 load Wire Size1 cable(s) AWG 14...AWG 2 (copper or aluminium) for load4 cable(s) AWG 6...400 kcmil (copper or aluminium) for line Electrical ConnectionTin plated aluminium lugs SCCRUp to 100 kA per UL 508 A ambient air temperature for operation-40...302 °F Block MaterialPhenolic block Terminal Tightening TorqueLug 45 lbf.in for AWG 6...AWG 4 (copper or aluminium) loadLug 40 lbf.in for AWG 8 (copper or aluminium) loadLug 35 lbf.in for AWG 14 (copper) loadLug 275 lbf.in for AWG 6...350 kcmil (copper or aluminium) lineLug 50 lbf.in for AWG 2 (copper or aluminium) loadLug 35 lbf.in for AWG 12...AWG10 (copper or aluminium) load wire stripping length1.06 in line connection0.56 in top load connection1 in bottom load connection height3.38 in width1.94 in depth2.61 in End Barrier9080LB33 Environment CertificationsCECSA file 70361 class 6228 01UL recognized E60616 CCN XCFR2 Ordering and shipping details Category21711 - 9080 LB Discount ScheduleCP1 GTIN00785901157090 Nbr. of units in pkg.1 Package weight(Lbs)1.5600000000000001 ReturnabilityY Country of originUS Offer Sustainability RoHS (date code: YYWW) REACh California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Lead and lead compounds, which is known to the State of California to cause cancer and birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsCADSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.