Power Distribution Block 1 Pole 1 Line 8 Load 600V 335A CU / 600V 270A ALShow more characteristics >
Product availabilityStock - Normally stocked in distribution facility
Main Range9080LB ProductPower Distribution Block Current Rating335 A for copper cable(s)270 A for aluminium cable(s) Short Circuit Current Rating65 kA Complementary System Voltage600 V AC/DC Mounting TypeSurface mount number of poles1 Terminals per Pole1 line8 load Wire Size1 cable(s) AWG 6...400 kcmil (copper or aluminium) for line8 cable(s) AWG 14...AWG 2 (copper or aluminium) for load Electrical ConnectionTin plated aluminium lugs SCCRUp to 100 kA per UL 508 A ambient air temperature for operation-40...302 °F Block MaterialPhenolic block Terminal Tightening TorqueLug 45 lbf.in for AWG 6...AWG 4 (copper or aluminium) loadLug 40 lbf.in for AWG 8 (copper or aluminium) loadLug 50 lbf.in for AWG 2 (copper or aluminium) loadLug 275 lbf.in for AWG 6...400 kcmil (copper or aluminium) lineLug 35 lbf.in for AWG 14...AWG 10 (copper or aluminium) load wire stripping length1.06 in line connection0.56 in top load connection1 in bottom load connection height4.75 in width2.28 in depth2.91 in End Barrier9080LB41 Environment CertificationsUL recognized E60616 CCN XCFR2CECSA file 70361 class 6228 01 Ordering and shipping details Category21711 - 9080 LB Discount ScheduleCP1 GTIN00785901097358 Nbr. of units in pkg.1 Package weight(Lbs)0.90000000000000002 ReturnabilityY Country of originUS Offer Sustainability RoHS (date code: YYWW) REACh California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Lead and lead compounds, which is known to the State of California to cause cancer and birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.