PRESSURE SWITCH 575VAC 5HP G +OPTIONSShow more characteristics >
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main device short nameG enclosure typeDust and damp proof weatherproof enclosure indoor/outdoor product specific applicationControl electrically driven water pumps and air compressors range of productSquare D Pumptrol switch applicationStandard Complementary adjustable range on rising pressure20...80 psi approximate adjustable differential20...40 psi depth3.68 in electrical connectionScrew clamp terminal fixing modeBy brackets fluid connection type0.25 inch NPSF internal height5.72 in materialZinc plated steel flange materials in contact with fluidNitrile (Buna-N) diaphragm maximum pressure100 psig motor power hp3 hp 115 V AC 3 phases5 hp 460/575 V AC 3 phases5 hp 460/575 V AC 1 phase2 hp 115 V AC 1 phase3 hp 230 V AC 1 phase5 hp 230 V AC 3 phases number of poles2 permissible voltage<= 575 V AC pressure actuatorDiaphragm product weight2.25 lb(US) range on decreasing pressure5...50 psi scale typeAdjustable differential switch functionDPST width3.44 in Environment NEMA degree of protectionNEMA 4 product certificationsUL listed file E12158 CCN NKPZCSA file LR25490 Ordering and shipping details Category21536 - 9013 G COMMERCIAL PRESSURE SWITCH Discount ScheduleCP7G GTIN00785901681373 Nbr. of units in pkg.1 Package weight(Lbs)19.5 ReturnabilityN Country of originMX Offer Sustainability RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable California proposition 65WARNING: This product can expose you to chemicals including: - - - - - - - Substance 1Diisononyl phthalate (DINP), which is known to the State of California to cause cancer, and - - - - - - - Substance 2Di-isodecyl phthalate (DIDP), which is known to the State of California to cause birth defects or other reproductive harm. - - - - - - - More informationFor more information go to www.p65warnings.ca.gov Contractual warranty Warranty period18 months
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.