|FA170423||ATV61 - EFlex - noise causing 4-20mA signal latching one 20mA.|
|FA163635||Where can I get support for APC and MGE Products?|
For support on APC and MGE products please visit: http://www.apc.com/support/
Additional Management Cards and Options
Air Cooled Chillers
|FA168203||Is there a product data sheet on the VW3G48101 ATS48 remote keypad?|
The ATS48 remote mounted keypad data sheet can be found in this FAQ attachment.
|FA168164||Where is detailed information for the ATS01 soft start?|
The catalog, document 8637CT0401, provides an abundance of information. Obtain the document online in Schneider Electric`s Technical Library or do...
|FA167047||How far does an NW breaker draw out from the cell in the withdrawn position? |
The change in position from connected to withdrawn is 14.25 inches.
|FA166698||Can 240V fuses be used in a QMB366W? |
No, however customer can use QMB366W for 240V application as long as he uses 600V fuses.
CTA-ID : 2060881
|FA166709||Where are the ground bars placed in standard I-line panels? |
Per the 80043-309-15 I-line Instruction Bulletin, page 27, the ground bar mounting locations are identified by the ground symbol, stamped in the backwall...
|FA166693||What are the dimensions and weights for the ATV61HC22N4? |
Width = 440 mm (17.32) (in.)
height = 1,190 mm (46.62) (in.)
Depth = 350 mm (13.78) (in.)
Weight = 163 kg...
|FA166359||What is the ATV61 drives part number for a variable torque application like a fan or pump?|
The ATV61 drives are rated to be used on light loads like Fan and pumps. They range from 1HP up to 900 HP @ 480VAC 3phase, 1HP to 125HP @ 230VAC...
|FA166358||What is the dissipated power for the ATV61 drives?|
See the attachment for dissipated power with drive mounted inside of the enclosure and dissipated power with drive mounted in flush mounting optional...