|FA167046||Can the EasyPact breaker be reverse fed? |
Yes, the EasyPact circuit breaker can be supplied from either the top or the bottom (reverse feeding) without any reduction in performance.
|FA167045||Is there a maximum number of receptacles that can be fed from one HOM-GFI breaker? |
No, but the circuit length must be under 250 ft. one way.
|FA166747||Will a QO3125SL subfeed lug kit fit into an NQ panelboard interior? |
Yes it will if application does not exede 125 Amps.
CTA-ID : 2058818
|FA166705||What are the blanks extensions HLW4EBL and HLN4EBL used for?|
HLW4EBL is for use with for H and J frame breakers with Micrologic trip units 5 or 6 mounting on the wide side of an I-line panelboard.
|FA166731||9037EG9: does this include the float & rod?|
No, it is just the float switch. The kits must be ordered separately.
CTA-ID : 2061853
|FA166707||How can you program the ATV212 Sflex to be reverse acting when using a 0-10V signal on VIB? They want 0V signal to be 60hz and 10V signal to be 0hz.|
Programmed the drive as follows:
F210 - 0 %
F211 - 60.0 Hz
F212 - 100 %
F213 - 0.0 Hz
and wire your 0-10vdc signal to VIB and CC
Fnod needs to be...
|FA166690||Can the ATV61 or ATV71 be installed in an ATEX environment?|
The ATV61 and ATV71 can be used in the functional safety loop for an ATEX application; however, they cannot be installed in the ATEX environment....
|FA166359||What is the ATV61 drives part number for a variable torque application like a fan or pump?|
The ATV61 drives are rated to be used on light loads like Fan and pumps. They range from 1HP up to 900 HP @ 480VAC 3phase, 1HP to 125HP @ 230VAC...
|FA164939||Do we have a way to field modify the Eflex drive to have an end of damper control?|
The EFlex install manual shows a addition of a 8501 relay if you order the Eflex drive with mod S09 from the factory. However there is a 2nd way...
|FA166254||How many spaces do 1p EDB**EPD breakers use ? |
Two pole spaces
CTA-ID : 2062104