|FA170982||Where do we send drives and soft starters back to get them repaired?|
Schneider Electric Industrial Repair Services
235 Burgess Rd. Greensboro NC 27409
Phone number is (336) 668-4848
FAX: 336.668.4878 ...
What is the replacement cover for the 9013 Type F Pressure Switch?|
Always include the complete part number with forms, when ordering a replacement cover.65076-792-56 is 9013 FHG Form M1 cover65076-792-54 is 9013 FRG...
|FA162001|| Do we have a filler plate for the obsolete NEHB panelboard?|
Yes. However the FP1 is now obsolete
CTA-ID : 2058473
What is the replacement part number for the fuse 25499-12821 for a Square D Series D Line Isolation Monitor - IGD?
The catalog number for the fuse for the IGD has been simplified to ``TR5``. CTA-ID : 2051005
|FA128357||Where do we repair our variable speed drives and soft starters?|
Electrical South, Inc. in Greensboro North Carolina
Phone: (800) 950-9550
Fax: (336) 668-4878
CTA-ID : 2049918
|FA169950||What is the Service entrance barrier for a QO342MQB200 that is CSA listed?|
The Service Entrance barrier is part number S1B76642 to be used in CSA listed products.
This was part number 4055903003 but has been modified to...
|FA107734||What is the catalog for replacement arrow pushbutton operators for an XACA201?|
XACA921 is up arrow and XACA922 is the down arrow. CTA-ID : 2014804
|FA169700||What are the repair parts for a H365DS Series E4 Heavy Duty Safety Switch? |
Answer The parts listed here are the only field replaceable parts.
Line base assembly - 40552-188-50 (3-required and arc suppressor assembly is not...
|FA169527||Where can I find a replacement Heatsink fan for my obsolete ATV58 or ATV66 series drive?|
We have had good success using Digikey equivalent fans in our ATV58 and ATV66 series drives. Contact Digikey at 1-800-344-4539 and have the original...
|FA169358||Breaker contact resistance, Proper testing procedure, Third party testing company is rejecting for breakers with bad contact resistance measurements.|
We have found that the most reliable technique to bring the contacts quickly to the approximate in-service condition is to apply an over current of...