|FA128201||Does the jumper on T1 and T2 on the terminal strip of a PGL breaker need to be removed if wired with a neutral CT?|
Yes. Remove and discard the shorting jumper from T1 and T2, if a CT is installed. The installation guide for that trip unit is: 48041-082-03.CTA-ID...
|FA128150||What is the Square D part number for a lug equivalent to Ilsco D3121 or CMC LA750-2|
Use Square part number 40251-136-50.CTA-ID : 2050012
|FA128027||Can the TVS120XR40S be wired to operate on a 120V 2 wire + G system?|
Yes. To make it work connect both black wires of the TVSS to the phase wire to make it work. However, we recommend the TVS120XRS for this application.CTA-ID...
|FA127881||What are the terminal numbers to connect an undervoltage trip coil on an H or J frame circuit breaker?|
Constant voltage at the correct level for the device (24V, 120V, AC, DC, etc) should be applied to terminals numbered D1 and D4. Designation for...
|FA127847||What is the lug size on a HU363DSWC and are there double lugs for it?|
The lug takes (1) # 12 - # 1/0 (Al) or (1) # 14 - # 1/0 (Cu). There are no double lugs available for this switch. CTA-ID : 2050310
|FA127833||Is it permissible to have parallel circuits being fed from the QO120AFI Arc-D-tect breaker?|
No. The QO-AFI breakers are not intended for parallel or multiple circuits.CTA-ID : 2050270
|FA127807||Can the 9001BW256 (ON-OFF Maintained) or any of the devices using contact symbol #10 be wired for a two wire control circuit?|
Yes, just wire to the N.O. ON contact. When it is pushed it will close and remain closed until the OFF button is pushed when it will then open. (The...
|FA127688||Can GV2, GV3 and GV7 starters be backfed ?|
Not recommended.CTA-ID : 2049249
|FA127241||How do you wire the shunt trip on a EDB34020SA breaker?|
Wire the switched hot 120 V wire to terminal 7 and the neutral to terminal 6.CTA-ID : 2049413
|FA127226||What is the acceptable wire size for a QOB-VH, 3 pole breaker 40 amp through 70 amp?|
These breakers will accept a #8 - #2 Cu/Al wire.CTA-ID : 2049025