|FA168587||What are the pinouts for the Micrologic trip unit Breaker comms module (BCM)?|
From left to right:
E3: Out- Black
E4 Out+ Red
E5: In- White
E6: In+ Green
This applies to Powerpact P, R and Masterpact NW,...
|FA167981||ATV312 tripping on ObF fault.|
If the drive trips while running, then check for power surges or spikes. Need to monitor for voltage surges and spikes. May need to install a line...
|FA167398||ATS01N212RT: The customer cannot get the soft start to run the motor.|
The ATS01N2**LU/QN/RT models require a run command on the control circuit.
A START/STOP contact can be wired to LI+ and LI2. This will allow soft...
|FA166884||How is a start command given to an ATS48?|
The ATS48 can start with either 2 wire or 3 wire control.
For 2 wire control: Wire a jumper between the STOP and RUN terminals. Close a dry contact...
|FA88143||Where would you put a 4-20 signal for speed reference instead of using a 0-10v on an Omegapak 8803?|
Need to connect the milliamp signal between OE1 (common) and EC. CTA-ID : 4042
|FA166828||How can ATS01N2...LU, QN, RT be started without control wires?|
Add a jumper between terminals LI+ and LI2. This provides a continuous RUN command. When power is supplied to the ATS01, it will immediately begin...
|FA92390||Where do you wire the speed potentiometer on the Omegapak 8803 Type P unit?|
The Speed pot is wired on terminals OE1, E1, P10 . The wiper goes to E1 terminal, P10 is the +10v and OE1 is com (0v). CTA-ID : 4045
|FA91123||Why does the speed potentiometer adjust speed in hand and auto for this 8804 Omegapak?|
With the E07 option card, if terminal 16 is tied to 78 the drive will use the POT for speed in hand and auto.Remove this jumper to allow a separate...
|FA166744||HCR548612U: what is the wire size for the incoming conductors?|
The lugs are rated for 4 - 3/0 thru 750kcmil cables but the UL wire bending range for the interior and box limits cable to 4-3/0 thru 500kcmil
|FA166719||How do I start and stop the motor on the SFlex 212 drive through the field terminals?|
This can be accomplished by closing and opening a dry contact connected between the field terminals P24 and F.
CNOD=0 and you will need a speed reference....