|FA167450||Can we get a 3/4`` hub in a 9001BR station?|
No, only the 1/2 inch NPT is available.
CTA-ID : 2062176
|FA167446||ATV312: What is the COS parameter?|
This is the Power Factor Parameter, located in the drC menu.
Look at the motor nameplate and use the power factor, typically designated as PF or...
|FA167441||Will the HMI part number VW3A28101 work with a ATV312 drive ?|
No. This is not a valid configuration.
CTA-ID : 2062168
|FA119519||How many spaces will a CAFI breaker take? |
Both QO and Homeline CAFI circuit breakers take one pole space. CTA-ID : 2031815
|FA167413||What is the command word for the ATS22 soft starters?|
The command word address for the ATS22 soft starter is 752.
The ETA status word address for the ATS22 soft stater is 256
See the attached PDF document...
|FA167391||Will two single-pole QO breakers mount in QO2100BNF?|
No, this enclosure is not for use with one-pole QO circuit breakers.
CTA-ID : 2062540
|FA167395||An ATS22 display is showing OHF (Over Heating Fault), but the starter has not been run for several hours and the ambient condition is very cold.|
The low end operating temperature for the ATS22 is 14 degrees F. Below this, the starter will fault and show OHF. OHF is an indication that the...
|FA167389||Does 9007CR53B2 include the 9007B head?|
Yes, it does.
CTA-ID : 2062486
|FA167392||What load centers use the PK2MB Retaining hold down kit? |
The PK2MB Retaining hold down kit is designed for use ONLY in the QO612L100F/S/RB/DF/DS, QO816L100F/S/RB/DF/DS and QO148L125GF/S/RB load centers....
|FA167394||What is the prefix H on the HL100WN2M16? |
The prefix H is for high temperature 0 to +350 degree F, and requires the use of the metal front cover .
The minimum temperature 0 degrees F is based...