|FA128147||Are the ATV21 and ATV212 drives plenum rated?|
The open type ATV21/ATV212 and the enclosed SFLEX are plenum rated. The SFLEX is stated in the brochure (8839BR0501R8/07) under environmental specs...
|FA170355||What is the case material for the Powerpact P breaker?|
The case material is R/C polyester plastic (QMFZ2), ref. CIC 25630 mfg. by Menzolit
CTA-ID : 2063143
|FA130527||Can the ATV12 keypad be used with the ATV312 or ATV32 drives?|
Yes, plus you need to order either the 1 or 3 meter ATV61/71 cable to use with it. CTA-ID : 2054051
|FA169529||Can the NEMA Class 8502 contactor be converted to a Class 8536 starter by installing an overload relay?|
The NEMA size 00, 0 & 1 contactors can be converted to starters by ordering and installing the appropriate replacement overload relay. However, due...
|FA109953||Is the 9 volt dc battery adapter available for the Class 9065 Type SP__ Motor Logic Plus solid state overload relay?|
This part is provided with each overload relay but is not available as a separate item.CTA-ID : 2019075
|FA169368||What is the difference between a GV2P20H7 and GV2P20? |
In the United States, only the `H7` version is used. The device label will have details that only apply to North America. The `H7` is not referenced...
|FA169363||What is the difference between a 2510KO2C and 2510KO6C non-reversing starter? |
The 2510KO2C has a 2HP@115VAC - 7.5HP@230VAC - 10HP@460/575VAC horsepower rating at 3 phase
The 2510KO6C has a 2HP@115VAC - 7.5HP@230VAC - 15HP@460VAC...
|FA169359||What exactly is a combination arc fault circuit interrupter or CAFI breaker?|
A combination arc fault circuit interrupter combines branch/feeder protection with outlet circuit protection.
The branch/feeder AFI breakers only...
|FA168589||The test button on a QO-GFI or HOM-GFI breaker will not trip the breaker; is the breaker bad?|
First ensure that the breaker is properly installed in an energized panel with the pigtail connected to the neutral bar.
If the breaker will not...
|FA168588||Does the new CAFI breaker have more arc-fault detection capabilities than the previous AFI breaker ? |
Yes, the CAFI breaker detects both series and parallel arcing. The AFI breaker detects parallel arcing only.
CTA-ID : 2063067