|FA129394||The elbow has been connected to the vault box 180 degs in the opposite direction. We need to re-do the connection between the elbow and the box. Need service to fix before the end of next week|
Elbow was rotated 180 degrees.CTA-ID : 2052775
|FA129365||What positions can the 9013FSG2 be mounted in?|
Any position. CTA-ID : 2052409
|FA129232||What is the maximum AC mains wire distance allowable to connect an SDSB1175C surge suppressor to a panelboard or load center?|
The wire length should be very short, about 18 inches from the panel bussing, maximum. Longer lengths drastically reduce the effectiveness of the...
|FA129125||What is the part number for the neutral bus kit for an 400A QMB panelboard?|
It is the QMB4SN.CTA-ID : 2051742
|FA129108||What standard applies to operating handle heights on switchgear?|
NEC 490.41The maximum height we should install any hand operated device is 6`6``(78 in.) unless it is a switch handle requiring more than 50 lbs....
|FA129072||LC1D12G7: How do you panel mount this?|
There are screw holes in the upper right and lower left corners of the contactorCTA-ID : 2051529
|FA129129||A customer is wanting to prepare a pad for some outdoor switchgear on order.|
How much distance should be allowed around the switchgear?
5 feet is recommended on all sides.CTA-ID : 2050972
|FA128929||Can a vertically mounted 8702SE or SF NEMA contactor be field converted to horizontal mounting?|
Yes, use a 9999SM12 horizontal interlock. The customer will have to supply their own power wiring.CTA-ID : 2051337
|FA128927||What are the torque requirements for QO wire binding screws and clamp plates?|
Scroll down for complete information.QO/QOB 10A - 30A, 1,2 and 3-pole, all interruption ratings: 36 lb.-in.QO/QOB 35 - 70A, 2 and 40 - 60A 3-pole,...
|FA128896||Does an energy efficient transformer have to be de-energized to install a weathershield?|
ABSOLUTELY!! Whenever work is being done on an electrical device, the power to the device needs to be turned off. In this case, the front and rear...